District heating (also known as heat networks or teleheating) is a system for distributing heat generated in a centralized location for residential and commercial heating requirements such as space heating and water heating. The heat is often obtained from a cogeneration plant burning fossil fuels but increasingly also biomass, although heat-only boiler stations, geothermal heating, heat pumps and central solar heating are also used, as well as nuclear power. District heating plants can provide higher efficiencies and better pollution control than localized boilers. According to some research, district heating with combined heat and power (CHPDH) is the cheapest method of cutting carbon emissions, and has one of the lowest carbon footprints of all fossil generation plants. A combination of CHP and centralized heat pumps are used in the Stockholm multi energy system. This allows the production of heat through electricity when there is an abundance of intermittent power production and cogeneration of electric power and district heating when the availability of intermittent power production is low.
Heat sources in use for various district heating systems include: power plants designed for combined heat and power (CHP, also called co-generation), including both combustion and nuclear power plants; and simple combustion of a fossil fuel or biomass; geothermal heat; solar heat; industrial heat pumps which extract heat from seawater, river or lake water, sewage, or waste heat from industrial processes.
District heat from combined heat and power or simple combustionEdit
The core element of many district heating systems is a heat-only boiler station. Additionally a cogeneration plant (also called combined heat and power, CHP) is often added in parallel with the boilers. Both have in common that they are typically based on combustion of primary energy carriers. The difference between the two systems is that, in a cogeneration plant, heat and electricity are generated simultaneously, whereas in heat-only boiler stations – as the name suggests – only heat is generated.
In the case of a fossil fueled cogeneration plant, the heat output is typically sized to meet half of the peak heat load but over the year will provide 90% of the heat supplied. The boiler capacity will be able to meet the entire heat demand unaided and can cover for breakdowns in the cogeneration plant. It is not economic to size the cogeneration plant alone to be able to meet the full heat load. In the New York City steam system, that is around 2.5 GW. Germany has the largest amount of CHP in Europe.
The combination of cogeneration and district heating is very energy efficient. A simple thermal power station can be 20–35% efficient, whereas a more advanced facility with the ability to recover waste heat can reach total energy efficiency of nearly 80%. Some may exceed 100% based on the lower heating value by condensing the flue gas as well.
Waste heat from nuclear power plants is sometimes used for district heating. The principles for a conventional combination of cogeneration and district heating applies the same for nuclear as it does for a thermal power station. Russia has several cogeneration nuclear plants which together provided 11.4 PJ of district heat in 2005. Russian nuclear district heating is planned to nearly triple within a decade as new plants are built.
Other nuclear-powered heating from cogeneration plants are in Ukraine, the Czech Republic, Slovakia, Hungary, Bulgaria, and Switzerland, producing up to about 100 MW per power station. One use of nuclear heat generation was with the Ågesta Nuclear Power Plant in Sweden closed in 1974.
Geothermal-sourced district heatEdit
This section needs expansion. You can help by adding to it. (May 2013)
Direct use geothermal district heating systems, which tap geothermal reservoirs and distribute the hot water to multiple buildings for a variety of uses, are uncommon in the United States, but have existed in America for over a century.
In 1890, the first wells were drilled to access a hot water resource outside of Boise, Idaho. In 1892, after routing the water to homes and businesses in the area via a wooden pipeline, the first geothermal district heating system was created.
As of a 2007 study, there were 22 geothermal district heating systems (GDHS) in the United States. As of 2010, two of those systems have shut down. The table below describes the 20 GDHS currently operational in America.
|System Name||City||State||Startup Year||Number of Customers||Capacity, MWt||Annual Energy Generated, GWh/year||System Temperature, °F||System Temperature, °C|
|Warm Springs Water District||Boise||ID||1892||275||3.6||8.8||175||79|
|Oregon Institute of Technology||Klamath Falls||OR||1964||1||6.2||13.7||192||89|
|College of Southern Idaho||Twin Falls||ID||1980||1||6.34||14||100||38|
|Pagosa Springs||Pagosa Springs||CO||1982||22||5.1||4.8||146||63|
|Idaho Capital Mall||Boise||ID||1982||1||3.3||18.7||150||66|
|San Bernardino||San Bernardino||CA||1984||77||12.8||22||128||53|
|City of Klamath Falls||Klamath Falls||OR||1984||20||4.7||10.3||210||99|
|Elko County School District||Elko||NV||1986||4||4.3||4.6||190||88|
|Gila Hot Springs||Glenwood||NM||1987||15||0.3||0.9||140||60|
|Fort Boise Veteran's Hospital Boise||Boise||ID||1988||1||1.8||3.5||161||72|
|Kanaka Rapids Ranch||Buhl||ID||1989||42||1.1||2.4||98||37|
|In Search Of Truth Community||Canby||CA||2003||1||0.5||1.2||185||85|
Solar-sourced district heatEdit
Use of solar heat for district heating has been increasing in Denmark and Germany in recent years. The systems usually include interseasonal thermal energy storage for a consistent heat output day to day and between summer and winter. Good examples are in Vojens at 50 MW, Dronninglund at 27 MW and Marstal at 13 MW in Denmark. These systems have been incrementally expanded to supply 10% to 40% of their villages' annual space heating needs. The solar-thermal panels are ground-mounted in fields. The heat storage is pit storage, borehole cluster and the traditional water tank. In Alberta, Canada the Drake Landing Solar Community has achieved a world record 97% annual solar fraction for heating needs, using solar-thermal panels on the garage roofs and thermal storage in a borehole cluster.
Heat pumps for district heatEdit
In Stockholm, the first heat pump was installed in 1977 to deliver district heating sourced from IBM servers. Today the installed capacity is about 660 MW heat, utilizing treated sewage water, sea water, district cooling, data centers and grocery stores as heat sources. Another example is the Drammen Fjernvarme District Heating project in Norway which produces 14 MW from water at just 8 °C, industrial heat pumps are demonstrated heat sources for district heating networks. Among the ways that industrial heat pumps can be utilized are:
- As the primary base load source where water from a low grade source of heat, e.g. a river, fjord, data center, power station outfall, sewage treatment works outfall (all typically between 0 ˚C and 25 ˚C), is boosted up to the network temperature of typically 60 ˚C to 90 ˚C using heat pumps. These devices, although consuming electricity, will transfer a heat output three to six times larger than the amount of electricity consumed. An example of a district system using a heat pump to source heat from raw sewage is in Oslo, Norway that has a heat output of 18 MW(thermal).
- As a means of recovering heat from the cooling loop of a power plant to increase either the level of flue gas heat recovery (as the district heating plant return pipe is now cooled by the heat pump) or by cooling the closed steam loop and artificially lowering the condensing pressure and thereby increasing the electricity generation efficiency.
- As a means of cooling flue gas scrubbing working fluid (typically water) from 60 ˚C post-injection to 20 ˚C pre-injection temperatures. Heat is recovered using a heat pump and can be sold and injected into the network side of the facility at a much higher temperature (e.g. about 80 ˚C).
- Where the network has reached capacity, large individual load users can be decoupled from the hot feed pipe, say 80 ˚C and coupled to the return pipe, at e.g. 40 ˚C. By adding a heat pump locally to this user, the 40 ˚C pipe is cooled further (the heat being delivered into the heat pump evaporator). The output from the heat pump is then a dedicated loop for the user at 40 ˚C to 70 ˚C. Therefore, the overall network capacity has changed as the total temperature difference of the loop has varied from 80–40 ˚C to 80 ˚C–x (x being a value lower than 40 ˚C).
Concerns have existed about the use of hydroflurocarbons as the working fluid (refrigerant) for large heat pumps. Whilst leakage is not usually measured, it is generally reported to be relatively low, such as 1% (compared to 25% for supermarket cooling systems). A 30-megawatt heatpump could therefore leak (annually) around 75 kg of R134a or other working fluid. Given the high global warming potential of some HFCs, this could equate to over 800,000 kilometres (500,000 mi) of car travel per year.
However, recent technical advances allow the use of natural heat pump refrigerants that have very low global warming potential (GWP). CO2 refrigerant (R744, GWP=1) or ammonia (R717, GWP=0) also have the benefit, depending on operating conditions, of resulting in higher heat pump efficiency than conventional refrigerants. An example is a 14 MW(thermal) district heating network in Drammen, Norway which is supplied by seawater-source heatpumps that use R717 refrigerant, and has been operating since 2011. 90 °C water is delivered to the district loop (and returns at 65 °C). Heat is extracted from seawater (from 60-foot (18 m) depth) that is 8 to 9 °C all year round, giving an average coefficient of performance (COP) of about 3.15. In the process the seawater is chilled to 4 °C; however, this resource is not utilized. In a district system where the chilled water could be utilized for air conditioning, the effective COP would be considerably higher.
In the future, industrial heat pumps will be further de-carbonised by using, on one side, excess renewable electrical energy (otherwise spilled due to meeting of grid demand) from wind, solar, etc. and, on the other side, by making more of renewable heat sources (lake and ocean heat, geothermal, etc.). Furthermore, higher efficiency can be expected through operation on the high voltage network.
Excess renewable electrical energy for district heatEdit
With European countries such as Germany and Denmark moving to very high levels (80% and 100% respectively by 2050) of renewable energy for all energy uses there will be increasing periods of excess production of renewable electrical energy. Storage of this energy as potential electrical energy (e.g. pumped hydro) is very costly and reduces total round-trip efficiency. However, storing it as heat in district heating systems, for use in buildings where there is demand, is significantly less costly. Whilst the quality of the electrical energy is degraded, high voltage grid MW sized heat pumps would maximise efficiency whilst not wasting excess renewable electricity. Stockholm at present has about 660 MW of heat pumps connected to its district heating system.
Heat accumulators and storageEdit
Increasingly large heat stores are being used with district heating networks to maximise efficiency and financial returns. This allows cogeneration units to be run at times of maximum electrical tariff, the electrical production having much higher rates of return than heat production, whilst storing the excess heat production. It also allows solar heat to be collected in summer and redistributed off season in very large but relatively low-cost in-ground insulated reservoirs or borehole systems. The expected heat loss at the 203,000m³ insulated pond in Vojens is about 8%.
After generation, the heat is distributed to the customer via a network of insulated pipes. District heating systems consist of feed and return lines. Usually the pipes are installed underground but there are also systems with overground pipes. Within the system heat storage units may be installed to even out peak load demands.
The common medium used for heat distribution is water or pressurized hot water, but steam is also used. The advantage of steam is that in addition to heating purposes it can be used in industrial processes due to its higher temperature. The disadvantage of steam is a higher heat loss due to the high temperature. Also, the thermal efficiency of cogeneration plants is significantly lower if the cooling medium is high-temperature steam, reducing electric power generation. Heat transfer oils are generally not used for district heating, although they have higher heat capacities than water, as they are expensive and have environmental issues.
At customer level the heat network is usually connected to the central heating system of the dwellings via heat exchangers (heat substations): the working fluids of both networks (generally water or steam) do not mix. However, direct connection is used in the Odense system.
Typical annual loss of thermal energy through distribution is around 10%, as seen in Norway's district heating network.
The amount of heat provided to customers is often recorded with a heat meter to encourage conservation and maximize the number of customers which can be served, but such meters are expensive. Due to the expense of heat metering, an alternative approach is simply to meter the water – water meters are much cheaper than heat meters, and have the advantage of encouraging consumers to extract as much heat as possible, leading to a very low return temperature, which increases the efficiency of power generation.
Many systems were installed under a socialist economy (such as in the former Eastern Bloc), and these were often not metered. This led to great inefficiencies – users simply opened windows when too hot – wasting energy and minimising the numbers of connectable customers.
Size of systemsEdit
District heating systems can vary in size. Some systems cover entire cities such as Stockholm or Flensburg, using a network of large 1000 mm diameter primary pipes linked to secondary pipes – 200 mm diameter perhaps, which in turn link to tertiary pipes of perhaps 25 mm diameter which might connect to 10 to 50 houses.
Some district heating schemes might only be sized to meet the needs of a small village or area of a city in which case only the secondary and tertiary pipes will be needed.
Some schemes may be designed to serve only a limited number of dwellings – 20–50 – in which case only tertiary sized pipes are needed.
Pros and consEdit
District heating has various advantages compared to individual heating systems. Usually district heating is more energy efficient, due to simultaneous production of heat and electricity in combined heat and power generation plants. This has the added benefit of reducing carbon emissions. The larger combustion units also have a more advanced flue gas cleaning than single boiler systems. In the case of surplus heat from industries, district heating systems do not use additional fuel because they recover heat which would otherwise be dispersed to the environment.
District heating requires a long-term financial commitment that fits poorly with a focus on short-term returns on investment. Benefits to the community include avoided costs of energy through the use of surplus and wasted heat energy, and reduced investment in individual household or building heating equipment. District heating networks, heat-only boiler stations, and cogeneration plants require high initial capital expenditure and financing. Only if considered as long-term investments will these translate into profitable operations for the owners of district heating systems, or combined heat and power plant operators. District heating is less attractive for areas with low population densities, as the investment per household is considerably higher. Also it is less attractive in areas of many small buildings; e.g. detached houses than in areas with a fewer larger buildings; e.g. blocks of flats, because each connection to a single-family house is quite expensive.
Individual heating systems can be completely shutdown intermittently according to local heating demand which is not the case with a district heating system.
It is doubtful District Heating is delivering the savings promised by many heat suppliers. Some customers are taking legal action against the supplier for Misrepresentation & Unfair Trading. The problem is so widespread the BBC TV, News & Radio, BBC TV, News & Radio, Guardian newspaper & consumer magazine all featured articles of concerning matters relating to the reliability of supply and costs.
There is also a growing concern about the use of oversized heat plates inside the HIU. Some customers use a 50 kW heat plate for the hot water and yet if they had a gas boiler at most would use 23 kW.
According to a London borough Council Report the performance gap of District Heating is different to what is promised.
Ownership, monopoly issues and charging structuresEdit
In many cases large combined heat and power district heating schemes are owned by a single entity. This was typically the case in the old Eastern bloc countries. However, for many schemes, the ownership of the cogeneration plant is separate from the heat using part.
Examples are Warsaw which has such split ownership with PGNiG Termika owning the cogeneration unit, the Dalkia Polska owning 85% of the heat distribution, the rest of the heat distribution is owned by municipality and workers. Similarly all the large CHP/CH schemes in Denmark are of split ownership.
Sweden provides an alternative example where the heating market is deregulated. In Sweden it is most common that the ownership of the district heating network is not separated from the ownership of the cogeneration plants, the district cooling network or the centralized heat pumps. There are also examples where the competition has spawned parallel networks and interconnected networks where multiple utilities cooperate.
In the United Kingdom there have been complaints that district heating companies have too much of a monopoly and are insufficiently regulated, an issue the industry is aware of, and has taken steps to improve consumer experience through the use of customer charters as set out by the heat trust.
Since conditions from city to city differ, every district heating system is unique. In addition, nations have different access to primary energy carriers and so they have a different approach on how to address heating markets within their borders.
Since 1954, district heating has been promoted in Europe by Euroheat & Power. They have compiled an analysis of district heating and cooling markets in Europe within their Ecoheatcool project supported by the European Commission. A separate study, entitled Heat Roadmap Europe, has indicated that district heating can reduce the price of energy in the European Union between now and 2050. The legal framework in the member states of the European Union is currently influenced by the EU's CHP Directive.
Cogeneration in EuropeEdit
The EU has actively incorporated cogeneration into its energy policy via the CHP Directive. In September 2008 at a hearing of the European Parliament's Urban Lodgment Intergroup, Energy Commissioner Andris Piebalgs is quoted as saying, "security of supply really starts with energy efficiency." Energy efficiency and cogeneration are recognized in the opening paragraphs of the European Union's Cogeneration Directive 2004/08/EC. This directive intends to support cogeneration and establish a method for calculating cogeneration abilities per country. The development of cogeneration has been very uneven over the years and has been dominated throughout the last decades by national circumstances.
As a whole, the European Union currently generates 11% of its electricity using cogeneration, saving Europe an estimated 35 Mtoe per annum. However, there are large differences between the member states, with energy savings ranging from 2% to 60%. Europe has the three countries with the world's most intensive cogeneration economies: Denmark, the Netherlands and Finland.
Other European countries are also making great efforts to increase their efficiency. Germany reports that over 50% of the country's total electricity demand could be provided through cogeneration. Germany set a target to double its electricity cogeneration from 12.5% of the country's electricity to 25% by 2020 and has passed supporting legislation accordingly in "Federal Ministry of Economics and Technology", (BMWi), Germany, August 2007. The UK is also actively supporting district heating. In the light of UK's goal to achieve an 80% reduction in carbon dioxide emissions by 2050, the government had set a target to source at least 15% of government electricity from CHP by 2010. Other UK measures to encourage CHP growth are financial incentives, grant support, a greater regulatory framework, and government leadership and partnership.
According to the IEA 2008 modelling of cogeneration expansion for the G8 countries, expansion of cogeneration in France, Germany, Italy and the UK alone would effectively double the existing primary fuel savings by 2030. This would increase Europe's savings from today's 155 TWh to 465 TWh in 2030. It would also result in a 16% to 29% increase in each country's total cogenerated electricity by 2030.
Governments are being assisted in their CHP endeavors by organizations like COGEN Europe who serve as an information hub for the most recent updates within Europe's energy policy. COGEN is Europe's umbrella organization representing the interests of the cogeneration industry, users of the technology and promoting its benefits in the EU and the wider Europe. The association is backed by the key players in the industry including gas and electricity companies, ESCOs, equipment suppliers, consultancies, national promotion organisations, financial and other service companies.
A 2016 EU energy strategy suggests increased use of district heating.
The largest district heating system in Austria is in Vienna (Fernwärme Wien) – with many smaller systems distributed over the whole country.
District heating in Vienna is run by Wien Energie. In the business year of 2004/2005 a total of 5.163 GWh was sold, 1.602 GWh to 251.224 private apartments and houses and 3.561 GWh to 5211 major customers. The three large municipal waste incinerators provide 22% of the total in producing 116 GWh electric power and 1.220 GWh heat. Waste heat from municipal power plants and large industrial plants account for 72% of the total. The remaining 6% is produced by peak heating boilers from fossil fuel. A biomass-fired power plant has produced heat since 2006.
In the rest of Austria the newer district heating plants are constructed as biomass plants or as CHP-biomass plants like the biomass district heating of Mödling or the biomass district heating of Baden.
Most of the older fossil-fired district heating systems have a district heating accumulator, so that it is possible to produce the thermal district heating power only at that time where the electric power price is high.
Bulgaria has district heating in around a dozen towns and cities. The largest system is in the capital Sofia, where there are four power plants (two CHPs and two boiler stations) providing heat to the majority of the city. The system dates back to 1949.
The largest district heating system in the Czech Republic is in Prague owned and operated by Pražská teplárenská, serving 265,000 households and selling c. 13 PJ of heat annually. Most of the heat is actually produced as waste heat in 30 km distant thermal power station in Mělník. There are many smaller central heating systems spread around the country including waste heat usage, municipal waste incineration and heat plants.
In Denmark district heating covers more than 60% of space heating and water heating. In 2007, 80.5% of this heat was produced by combined heat and power plants. Heat recovered from waste incineration accounted for 20.4% of the total Danish district heat production. In 2013, Denmark imported 158,000 ton waste for incineration. Most major cities in Denmark have big district heating networks, including transmission networks operating with up to 125 °C and 25 bar pressure and distribution networks operating with up to 95 °C and between 6 and 10 bar pressure. The largest district heating system in Denmark is in the Copenhagen area operated by CTR I/S and VEKS I/S. In central Copenhagen, the CTR network serves 275,000 households (90-95% of the area's population) through a network of 54 km double district heating distribution pipes providing a peak capacity of 663 MW. The consumer price of heat from CTR is approximately €49 per MWh plus taxes (2009).
In Finland district heating accounts for about 50% of the total heating market, 80% of which is produced by combined heat and power plants. Over 90% of apartment blocks, more than half of all terraced houses, and the bulk of public buildings and business premises are connected to a district heating network. Natural gas is mostly used in the south-east gas pipeline network, imported coal is used in areas close to ports, and peat is used in northern areas where peat is a natural resource. Other renewables, such as wood chips and other paper industry combustible by-products, are also used, as is the energy recovered by the incineration of municipal solid waste. Industrial units which generate heat as an industrial by-product may sell otherwise waste heat to the network rather than release it into the environment. Excess heat and power from pulp mill recovery boilers is a significant source in mill towns. In some towns waste incineration can contribute as much as 8% of the district heating heat requirement. Availability is 99.98% and disruptions, when they do occur, usually reduce temperatures by only a few degrees.
In Germany district heating has a market share of around 14% in the residential buildings sector. The connected heat load is around 52.729 MW. The heat comes mainly from cogeneration plants (83%). Heat-only boilers supply 16% and 1% is surplus heat from industry. The cogeneration plants use natural gas (42%), coal (39%), lignite (12%) and waste/others (7%) as fuel.
The largest district heating network is located in Berlin whereas the highest diffusion of district heating occurs in Flensburg with around 90% market share. In Munich about 70% of the electricity produced comes from district heating plants.
District heating has rather little legal framework in Germany. There is no law on it as most elements of district heating are regulated in governmental or regional orders. There is no governmental support for district heating networks but a law to support cogeneration plants. As in the European Union the CHP Directive will come effective, this law probably needs some adjustment.
Greece has district heating mainly in the Province of Western Macedonia, Central Macedonia and the Peloponnese Province. The largest system is the city of Ptolemaida, where there are five power plants (thermal power stations or TPS in particular) providing heat to the majority of the largest towns and cities of the area and some villages. The first small installation took place in Ptolemaida in 1960, offering heating to Proastio village of Eordaea using the TPS of Ptolemaida. Today District heating installations are also available in Kozani, Ptolemaida, Amyntaio, Philotas, Serres and Megalopolis using nearby power plants. In Serres the power plant is a Hi-Efficiency CHP Plant using natural gas, while coal is the primary fuel for all other district heating networks.
According to the 2011 census there were 607,578 dwellings (15.5% of all) in Hungary with district heating, mostly panel flats in urban areas. The largest district heating system located in Budapest, the municipality-owned Főtáv Zrt. ("Metropolitan Teleheating Company") provides heat and piped hot water for 238,000 households and 7,000 companies.
With 95% of all housing (mostly in the capital of Reykjavík) enjoying district heating services – mainly from geothermal energy, Iceland is the country with the highest penetration of district heating.
Most of Iceland's district heating comes from three geothermal power plants, producing over 800 MWth:
- Svartsengi combined heat and power plant (CHP)
- Nesjavellir CHP plant
- Hellisheiði CHP plant
The Dublin Waste-to-Energy Plant will provide district heating for up to 50,000 homes in Poolbeg and surrounding areas. Tralee in Co Kerry has a 1 MW district heating system providing heat to an apartment complex, sheltered housing for the elderly, a library and over 100 individual houses. The system is fuelled by locally produced wood chip.
In Glenstal Abbey in Co Limerick there exists a pond-based 150 kW heating system for a school.
In Italy, district heating is used in some cities (Bergamo, Brescia, Cremona, Bolzano, Ferrara, Imola, Reggio Emilia, Terlan, Turin, Lodi, and now Milan). The district heating of Turin is the biggest of the country and it supplies 550.000 people (62% of the whole city population).
Cityheating in Rotterdam.
In Norway district heating only constitutes approximately 2% of energy needs for heating. This is a very low number compared to similar countries. One of the main reasons district heating has a low penetration in Norway is access to cheap hydro-based electricity, and 80% of private electricity consumption goes to heat rooms and water. However, there is district heating in the major cities.
In 2009, 40% of Polish households used district heating, most of them in urban areas. Heat is provided primarily by combined heat and power plants, most of which burn hard coal. The largest district heating system is in Warsaw, owned and operated by Veolia Warszawa, distributing approx. 34 PJ annually.
The largest district heating system in Romania is in Bucharest. Owned and operated by RADET, it distributes approximately 24 PJ annually, serving 570 000 households. This corresponds to 68% of Bucharest's total domestic heat requirements (RADET fulfills another 4% through single-building boiler systems, for a total of 72%).
In most Russian cities, district-level combined heat and power plants (ТЭЦ, теплоэлектроцентраль) produce more than 50% of the nation's electricity and simultaneously provide hot water for neighbouring city blocks. They mostly use coal and oil-powered steam turbines for cogeneration of heat. Now, gas turbines and combined cycle designs are beginning to be widely used as well. A Soviet-era approach of using very large central stations to heat large districts of a big city or entire small cities is not fading away even notwithstading to inefficiency of the old networks, where much heat is lost in the piping network because of leakages and lack of proper thermal insulation.
In Serbia, district heating is used throughout the main cities, particularly in the capital, Belgrade. The first district heating plant was built in 1961 as a means to provide effective heating to the newly built suburbs of Novi Beograd. Since then, numerous plants have been built to heat the ever-growing city. They use natural gas as fuel, because it has less of an effect on the environment. The district heating system of Belgrade possesses 112 heat sources of 2,454 MW capacity, over 500 km of pipeline, and 4365 connection stations, providing district heating to 240,000 apartments and 7,500 office/commercial buildings of total floor area exceeding 17,000,000 square meters.
Sweden has a long tradition for using district heating in urban areas. In 2015, about 60% of Sweden's houses (private and commercial) were heated by district heating, according to the Swedish association of district heating. The city of Växjö reduced its fossil fuel consumption by 30% between 1993 and 2006, and aimed for a 50% reduction by 2010. This was to be achieved largely by way of biomass fired teleheating. Another example is the plant of Enköping, combining the use of short rotation plantations both for fuel as well as for phytoremediation.
47% of the heat generated in Swedish teleheating systems are produced with renewable bioenergy sources, as well as 16% in waste-to-energy plants, 7% is provided by heat pumps, 10% by flue-gas condensation and 6% by industrial waste heat recovery. The remaining are mostly fossil fuels: oil (3%), natural gas (3%), peat (2%), and coal (1%).
In the United Kingdom, district heating became popular after World War II, but on a restricted scale, to heat the large residential estates that replaced areas devastated by the Blitz. In 2013 there were 1,765 district heating schemes with 920 based in London alone. In total around 210,000 homes and 1,700 businesses are supplied by heat networks in the UK.
The Pimlico District Heating Undertaking (PDHU) first became operational in 1950 and continues to expand to this day. The PDHU once relied on waste heat from the now-disused Battersea Power Station on the South side of the River Thames. It is still in operation, the water now being heated locally by a new energy centre which incorporates 3.1 MWe / 4.0 MWth of gas fired CHP engines and 3 × 8 MW gas-fired boilers.
One of the United Kingdom's largest district heating schemes is EnviroEnergy in Nottingham. The plant initially built by Boots is now used to heat 4,600 homes, and a wide variety of business premises, including the Concert Hall, the Nottingham Arena, the Victoria Baths, the Broadmarsh Shopping Centre, the Victoria Centre, and others. The heat source is a waste-to-energy incinerator. Scotland has several district heating systems with the first in the UK being installed at Aviemore and others following at Lochgilphead, Fort William and Forfar.
Sheffield's district heating network was established in 1988 and is still expanding today. It saves an equivalent 21,000 plus tonnes of CO2 each year when compared to conventional sources of energy – electricity from the national grid and heat generated by individual boilers. There are currently over 140 buildings connected to the district heating network. These include city landmarks such as the Sheffield City Hall, the Lyceum Theatre, Sheffield University, Sheffield Hallam University, hospitals, shops, offices and leisure facilities plus 2,800 homes. More than 44 km of underground pipes deliver energy which is generated at Sheffield Energy Recovery Facility. This converts 225,000 tonnes of waste into energy, producing up to 60 MWe of thermal energy and up to 19 MWe of electrical energy.
The Southampton District Energy Scheme was originally built to use just geothermal energy, but now also uses the heat from a gas fired CHP generator. It supplies heating and district cooling to many large premises in the city, including the WestQuay shopping centre, the De Vere Grand Harbour hotel, the Royal South Hants Hospital, and several housing schemes.
Lerwick District Heating Scheme is of note because it is one of the few schemes where a completely new system was added to a previously existing small town.
ADE has an online map of district heating installations in the UK. ADE estimates that 54 percent of energy used to produce electricity is being wasted via conventional power production, which relates to £9.5 billion ($US12.5 billion) per year.
In North America, district heating systems fall into two general categories. Those that are owned by and serve the buildings of a single entity are considered institutional systems. All others fall into the commercial category.
District Heating is becoming a growing industry in Canadian cities, with many new systems being built in the last ten years. Some of the major systems in Canada include:
- Calgary: ENMAX currently operates the Calgary Downtown District Energy Centre which provides heating to up to 10,000,000 square feet (930,000 m2) of new and existing residential and commercial buildings. The District Energy Centre began operations in March 2010 providing heat to its first customer, the City of Calgary Municipal building.
- Hamilton, ON has a district heating and cooling system in the downtown core, operated by HCE Energy Inc.
- Montreal has a district heating and cooling system in the downtown core.
- Toronto – Enwave provides district heating and cooling within the downtown core of Toronto, including deep lake cooling technology, which circulates cold water from Lake Ontario through heat exchangers to provide cooling for many buildings in the city.
- Surrey: Surrey City Energy owned by the city, provides district heating to the city's City Centre district.
- Central Heat Distribution Ltd. Since 1968 operates a central heating plant in the downtown core of Vancouver, British Columbia. In addition to heating 180 buildings, the Central Heat Distribution network also drives a steam clock.
- A large scale district heating system known as the Neighbourhood Energy Utility in the South East False Creek area is in initial operations with natural gas boilers and serves the 2010 Olympic Village. The commissioning of an innovative untreated sewage heat recovery system anticipated for January 2010 is expected to supply 70% of annual energy demands and reduce greenhouse gas emissions.
- Windsor, Ontario has a district heating and cooling system in the downtown core.
- Drake Landing, AB, is small in size (52 homes) but notable for having the only central solar heating system in North America.
- London, Ontario and Charlottetown, PEI have district heating co-generation systems owned and operated by Veresen.
- Sudbury, Ontario has a district heating cogeneration system in its downtown core, as well as a standalone cogeneration plant for the Sudbury Regional Hospital. In addition, Naneff Gardens, a new residential subdivision off Donnelly Drive in the city's Garson neighbourhood, features a geothermal district heating system using technology developed by a local company, Renewable Resource Recovery Corporation.
- Ottawa, contains a significant district heating and cooling system serving the large number of federal government buildings in the city. The system loop contains nearly a million gallons of chilled or heated water at any time.
- Cornwall, Ontario operates a district heating system which serves a number of city buildings and schools.
- Markham, Ontario: Markham District Energy operates several district heating sites:
- Warden Energy Centre (c. 2000), Clegg Energy Centre and Birchmount Energy Centre serving customers in the Markham Centre area
- Bur Oak Energy Centre (c. 2012) serving customers in the Cornell Centre area
Many Canadian universities operate central campus heating plants.
The Holly Steam Combination Company was the first steam heating company to commercially distribute district heating from a central steam heating system.
- Consolidated Edison of New York (Con Ed) operates the New York City steam system, the largest commercial district heating system in the United States. The system has operated continuously since March 3, 1882 and serves Manhattan Island from the Battery through 96th Street. In addition to providing space- and water-heating, steam from the system is used in numerous restaurants for food preparation, for process heat in laundries and dry cleaners, and to power absorption chillers for air conditioning.
The city of Milwaukee, Wisconsin has been using district heating for its central business district since the Valley Power Plant commenced operations in 1968. Amazingly, the air quality in the immediate vicinity of the plant, based on the sensor located on César Chavez Drive, qualifies as the best in Southeastern Wisconsin, at least with regard to ozone concentration. The recent (2012) conversion of the plant, which changed the fuel input from coal to natural gas, is expected to further improve air quality at both the local César Chavez sensor as well as Antarctic sensors . Interesting to note about Wisconsin power plants is their dual use as breeding grounds for peregrines .
- On July 18, 2007, one person was killed and numerous others injured when a steam pipe exploded on 41st Street at Lexington. On August 19, 1989, three people were killed in an explosion in Gramercy Park.
- Denver's district steam system is the oldest continuously operated commercial district heating system in the world. It began service November 5, 1880 and continues to serve 135 customers. The system is partially powered by the Xcel Energy Zuni Cogeneration Station, which was originally built in 1900.
- NRG Energy operates district systems in the cities of San Francisco, Harrisburg, Minneapolis, Omaha, Pittsburgh, and San Diego.
- Seattle Steam Company operates a district system in Seattle.
- Hamtramck Energy Services (HES) operates a district system in Detroit that started operation at the Willis Avenue Station in 1903.
- Lansing Board of Water and Light, a municipal utility system in Lansing, Michigan operates a heated and chilled water system from their existing coal plant. They have announced their new natural gas cogeneration plant will continue to provide this service.
- Cleveland Thermal operates a district steam (since 1894) from the Canal Road plant near The Flats and district cooling system (since 1993) from Hamilton Avenue plant on the bluffs east of downtown.
- Fort Chicago Energy Partners L.P. operate district heating/co-generation plants in Ripon, California and San Gabriel, California.
- Veolia Energy, a successor of the 1887 Boston Heating Company, operates a 26-mile (42 km) district system in Boston and Cambridge, Massachusetts, and also operates systems in Philadelphia PA, Baltimore MD, Kansas City MO, Tulsa OK, Houston TX and other cities.
- District Energy St. Paul operates the largest hot water district heating system in North America and generates the majority of its energy from an adjacent biomass-fueled combined heat and power plant. In March 2011, a 1 MWh thermal solar array was integrated into the system, consisting of 144 20' x 8' solar panels installed on the roof of a customer building, RiverCentre.
- The California Department of General Services runs a central plant providing district heating to four million square feet in 23 state-owned buildings, including the State Capitol, using high-pressure steam boilers.
District heating is also used on many college campuses, often in combination with district cooling and electricity generation. Colleges using district heating include the University of Texas at Austin; Rice University; Brigham Young University; Georgetown University; Cornell University, which also employs deep water source cooling using the waters of nearby Cayuga Lake; Purdue University; University of Notre Dame; Michigan State University; Eastern Michigan University; Case Western Reserve University; Iowa State University; University of Delaware; University of Maryland, College Park, University of Wisconsin–Madison, and several campuses of the University of California. MIT installed a cogeneration system in 1995 that provides electricity, heating and cooling to 80% of its campus buildings. The University of New Hampshire has a cogeneration plant run on methane from an adjacent landfill, providing the University with 100% of its heat and power needs without burning oil or natural gas. North Dakota State University (NDSU) in Fargo, North Dakota has used district heating for over a century from their coal-fired heating plant.
87 district heating enterprises are operating in Japan, serving 148 districts.
Many companies operate district cogeneration facilities that provide steam and/or hot water to many of the office buildings. Also, most operators in the Greater Tokyo serve district cooling.
This article needs additional citations for verification. (December 2014) (Learn how and when to remove this template message)
In southern China, there are nearly no district heating systems. In northern China, district heating systems are common. Most district heating system which are just for heating instead of CHP use hard coal. For air pollution in China has become quite serious, many cities gradually are now using natural gas rather than coal in district heating system. There is also some amount of geothermal heating and sea heat pump systems.
District heating traces its roots to the hot water-heated baths and greenhouses of the ancient Roman Empire. District systems gained prominence in Europe during the Middle Ages and Renaissance, with one system in France in continuous operation since the 14th century. The U.S. Naval Academy in Annapolis began steam district heating service in 1853.
Although these and numerous other systems have operated over the centuries, the first commercially successful district heating system was launched in Lockport, New York, in 1877 by American hydraulic engineer Birdsill Holly, considered the founder of modern district heating.
In the 1980s Southampton began utilising combined heat and power district heating, taking advantage of geothermal heat "trapped" in the area. The geothermal heat provided by the well works in conjunction with the Combined Heat and Power scheme. Geothermal energy provides 15-20%, fuel oil 10%, and natural gas 70% of the total heat input for this scheme and the combined heat and power generators use conventional fuels to make electricity. "Waste heat" from this process is recovered for distribution through the 11 km mains network.
Penetration of district heating (DH) into the heat market varies by country. Penetration is influenced by different factors, including environmental conditions, availability of heat sources, economics, and economic and legal framework.
In the year 2000 the percentage of houses supplied by district heat in some European countries was as follows:
In Iceland the prevailing positive influence on DH is availability of easily captured geothermal heat. In most Eastern European countries, energy planning included development of cogeneration and district heating. Negative influence in the Netherlands and UK can be attributed partially to milder climate, along with competition from natural gas. The tax on domestic gas prices in the UK is a third of that in France and a fifth of that in Germany.
- District cooling
- Central solar heating
- CHP Directive
- Geothermal heating
- Lists of public utilities
- List of district heating systems
- New York City steam system
- Public utility
- Thermal energy storage
- Deep lake water cooling
- Energy policy of the European Union
- Relative cost of electricity generated by different sources
- Alchevsk district heating disaster (2006)
- "Carbon footprints of various sources of heat – CHPDH comes out lowest | Claverton Group". Claverton-energy.com. Retrieved 2011-09-25.
- Levihn, Fabian (2017). "CHP and heat pumps to balance renewable power production: Lessons from the district heating network in Stockholm". Energy. doi:10.1016/j.energy.2017.01.118. Retrieved 2017-03-15.
- "Newsroom: Steam". ConEdison. Retrieved 2007-07-20.
- Bevelhymer, Carl (2003-11-10). "Steam". Gotham Gazette. Archived from the original on 2007-08-13. Retrieved 2007-07-20.
- What is cogeneration? COGEN Europe, 2015
- "DOE – Fossil Energy: How Turbine Power Plants Work". Fossil.energy.gov. Archived from the original on August 12, 2011. Retrieved 2011-09-25.
- "Waste-to-Energy CHP Amager Bakke Copenhagen". Retrieved 2015-03-09.
- "Nuclear Power in Russia". World-nuclear.org. 2011-09-21. Retrieved 2011-09-25.
- SUGIYAMA KEN'ICHIRO (Hokkaido Univ.) et al. /000020060706A0175205.php Nuclear District Heating: The Swiss Experience[permanent dead link]
- Bloomquist, R. Gordon (2001). Geothermal District Energy System Analysis, Design, and Development (PDF). International Summer School. International Geothermal Association. p. 213(1). Retrieved November 28, 2015. Lay summary – Stanford University.
During Roman times, warm water was circulated through open trenches to provide heating for buildings and baths in Pompeii.
- Thorsteinsson, Hildigunnur. "U.S. Geothermal District Heating: Barriers and Enablers" (PDF). Archived from the original (PDF) on 9 August 2014. Retrieved 25 July 2014.
- Lund, John. "The United States of America Country Update 2010" (PDF). Retrieved 25 July 2014.
- Schmidt T., Mangold D. (2013). Large-scale thermal energy storage – Status quo and perspectives. First international SDH Conference, Malmö, SE, 9-10th April 2013. Powerpoint.
- Wittrup, Sanne (23 October 2015). "Fjernvarmeværker går fra naturgas til sol". Ingeniøren.
- Wittrup, Sanne (14 June 2015). "Verdens største damvarmelager indviet i Vojens". Ingeniøren.
- Holm L. (2012). Long Term Experiences with Solar District Heating in Denmark[permanent dead link]. European Sustainable Energy Week, Brussels. 18–22 June 2012. Powerpoint.
- Current data on Danish solar heat plants (click Vojens in South-West Denmark, then "About the plant")
- Dalenbäck, J-O (2012). Large-Scale Solar Heating: State of the Art[permanent dead link]. Presentation at European Sustainable Energy Week, 18–22 June 2012, Brussels, Belgium.
- Wong B., Thornton J. (2013). Integrating Solar & Heat Pumps. Renewable Heat Workshop. (Powerpoint)
- Natural Resources Canada, 2012. Canadian Solar Community Sets New World Record for Energy Efficiency and Innovation. 5 Oct. 2012.
- Pedersen, S. & Stene, J. (2006). 18 MW heat pump system in Norway utilises untreated sewage as heat source. IEA Heat Pump Centre Newsletter, 24:4, 37–38.
- Hoffman, & Pearson, D. 2011. Ammonia heat pumps for district heating in Norway 7 – a case study. Presented at Institute of Refrigeration, 7 April, London.
- http://setis.ec.europa.eu/system/files/JRCDistrictheatingandcooling.pdf Combined Heat and Power and District Heating report. Joint Research Centre, Petten, under contract to European Commission, DG Energy 2013
- DYRELUND Anders, Ramboll, 2010. Heat Plan Denmark 2010. .
- "Norwegian Water Resources and Energy Directorate" (PDF). Archived from the original (PDF) on 2011-09-28. Retrieved 2011-09-25.
- Dunne, Eimear. "Infographic explaining District Heating Systems". Frontline Energy & Environmental. Archived from the original on 5 May 2014. Retrieved 5 May 2014.
- Dowling, Nicola; Goldberg, Adrian (30 April 2017). "Green scheme 'causing fuel poverty'". Retrieved 18 March 2018 – via www.bbc.co.uk.
- Green heating system accused of causing 'fuel poverty' BBC
- Connolly, David; Mathiesen, Brian Vad; Østergaard, Poul Alberg; Möller, Bernd; Nielsen, Steffen; Lund, Henrik; Persson, Urban; Werner, Sven; Grözinger, Jan; Boermans, Thomas; Bosquet, Michelle; Trier, Daniel (27 May 2013). "Heat Roadmap Europe 2: Second Pre-Study for the EU27". Department of Development and Planning, Aalborg University. Retrieved 18 March 2018 – via vbn.aau.dk.
- "Energy Efficiency Industrial Forum Position Paper: energy efficiency – a vital component of energy security" (PDF).[permanent dead link]
- "COGEN Europe News". Archived from the original on 2009-01-01.
- "COGEN Europe: Cogeneration in the European Union's Energy Supply Security" (PDF).[permanent dead link]
- "DEFRA Action in the UK – Combined Heat and Power". Archived from the original on 2010-06-12.
- Steyr, Fernwärme. "Bioenergie Steyr". www.fernwaermesteyr.at. Retrieved 18 March 2018.
- www.tscr.cz, Teplárenské sdružení České republiky -. "Teplárenské sdružení ČR - sdružuje teplárny a podnikatele v teplárenství a energetice". www.tscr.cz. Retrieved 18 March 2018.
- Kort om elforsyning i Danmark, from the Homepage of Dansk Energi (in Danish). Archived March 2, 2009, at the Wayback Machine.
- Danish Energy Statistics 2007[permanent dead link] by the Danish Ministry of Energy (in Danish).
- Klimaråd: Affaldsimport vil belaste dansk CO2-regnskab 27 November 2015.
- Environmentally Friendly District Heating to Greater Copenhagen Archived November 29, 2007, at the Wayback Machine., publication by CTR I/S (2006)
- Prisen på Fjernvarme Archived July 19, 2011, at the Wayback Machine., price list from the Danish homepage of a Copenhagen district heating provider Københavns Energi Archived June 11, 2004, at the Wayback Machine.
- "Network - DAC". dac.dk. Retrieved 18 March 2018.
- District heating in Finland Archived July 22, 2011, at the Wayback Machine.
- "In Helsinki". Scientificamerican.com. Retrieved 2011-09-25.
- "Underground data center to help heat Helsinki | Green Tech – CNET News". News.cnet.com. 2009-11-29. Retrieved 2011-09-25.
- AGFW Branchenreport 2006 Archived September 27, 2007, at the Wayback Machine., by the German Heat and Power Association -AGFW- (in German).
- "Combined heat and power". www.swm.de. Retrieved 18 March 2018.
- Hungarian census 2011 table 1.2.10 (Hungarian)
- "Cégünkről". FŐTÁV – Budapesti Távhőszolgáltató Zrt. Retrieved 18 March 2018.
- "History of District Heating in Iceland". Mannvit.com. Retrieved 2011-09-25.
- Sean Duke (August 9, 2016). "An 'under the hood' look at Dublin's First 'waste-to-energy' plant". Science Spinning.
- "Archived copy" (PDF). Archived from the original (PDF) on 2014-05-06. Retrieved 2014-05-06.
- "Zużycie energii w gospodarstwach domowych w 2009 r" [Energy consumption in households in 2009] (PDF) (in Polish). Główny Urząd Statystyczny. 2012-05-28. Retrieved 2013-01-25.
- "В Сибири и Якутии ждут подачи тепла". BBC News. January 4, 2008. Retrieved May 1, 2010.
-  Svensk Fjärrvärme
- [permanent dead link] Municipality of Växjö
- Mola-Yudego, B; Pelkonen, P. (2011). "Pulling effects of district heating plants on the adoption and spread of willow plantations for biomass: The power plant In Enköping (Sweden)". Biomass and Bioenergy. 35 (7): 2986–2992. doi:10.1016/j.biombioe.2011.03.040. Retrieved 2012-10-14.
-  Svensk Fjärrvärme
- J.Wawrzynczyk, M. Recktenwald, O. Norrlöw and E. Szwajcer Dey (March 2008). "The role of cation-binding agents and enzymes in solubilisation of sludge" (PDF). Water Research. 42 (6,7): 1555–1562. doi:10.1016/j.watres.2007.11.004. Retrieved 16 April 2013.
- "Summary evidence on District Heating Networks in the UK" (PDF). DECC.
- "The Future of Heating : Meeting the Challenge" (PDF). DECC.
- "District Heating Installation Map". ADE.
- Lambert, Kirsty (9 November 2017). "What a Waste! The Big Problem of Heat Loss in UK Cities". www.renewableenergyworld.com. Retrieved 12 November 2017.
- "NOTICIAS – Bioenergy International España: revista especializada en bioenergía". Bioenergyinternational.es. 2011-01-18. Archived from the original on 2011-09-10. Retrieved 2011-09-25.
- "ENMAX District Energy Centre". ENMAX.com. Retrieved 2015-09-25.
- "HCE Energy Inc". hamiltonce.com. Retrieved 2015-12-18.
- Reid, Amy (November 30, 2017). "An exclusive look at Surrey's expanding district energy system". Surrey Now-Leader. Retrieved January 28, 2018.
- "Neighbourhood Energy Utility". Vancouver.ca. Retrieved 2011-09-25.
- "New geothermal technology could cut energy costs". Northern Life, August 12, 2009.
- "Con Ed Steam". Energy.rochester.edu. Archived from the original on 2007-09-21. Retrieved 2011-09-25.
- "A Brief History of Con Edison". Con Edison. Archived from the original on 2015-11-14. Retrieved 2014-05-04.
- "Explosion rocks central New York". BBC News. July 19, 2007. Retrieved May 1, 2010.
- Barron, James (July 19, 2007). "Steam Blast Jolts Midtown, Killing One". The New York Times. Retrieved May 1, 2010.
- Jan Wagner; Stephen P. Kutska (October 2008). Monica Westerlund, ed. "DENVER'S 128-YEAR-OLD STEAM SYSTEM: "THE BEST IS YET TO COME"". District Energy. 94 (4): 16–20. ISSN 1077-6222.
- "TemplatePowerplant". Archived from the original on 28 June 2010. Retrieved 20 July 2010.
Plant Description: ... The facility also supplies steam for delivery to Xcel Energy's thermal energy customers in downtown Denver. ... Plant History: Zuni Station was originally built in 1900 and called the LaCombe Plant.
- "District energy | combined heat and power plants | NRG Thermal Corporation". Nrgthermal.com. Retrieved 2011-09-25.
-  Archived August 11, 2010, at the Wayback Machine.
- "Theodore Newton Vail and the Boston Heating Company, 1886–1890". Energy.rochester.edu. Archived from the original on 2009-07-18. Retrieved 2010-05-13.
- "SACRAMENTO CENTRAL UTILITY PLANT – CASE STUDY" (PDF). Alerton.com. Retrieved 2013-10-25.
- "Energy Consumption - Sustainability at Rice University". sustainability.rice.edu. Retrieved 18 March 2018.
- "BYU Central Utilities Plant". apmonitor.com. Retrieved 18 March 2018.
- "Energy and Climate". sustainability.georgetown.edu. Retrieved 18 March 2018.
- "Combined Heat and Power Plant". energyandsustainability.fs.cornell.edu. Retrieved 18 March 2018.
- "Custom content goes here". energyandsustainability.fs.cornell.edu. Retrieved 18 March 2018.
- "Archived copy". Archived from the original on 2013-12-25. Retrieved 2013-12-24.
- "Eastern Michigan University: Physical Plant". www.emich.edu. Retrieved 18 March 2018.
- "Heating & Cooling Plants – Physical Plant – UW–Madison". physicalplant.wisc.edu. Retrieved 18 March 2018.
- "University of California cogeneration plant gets its power back". Retrieved 2015-12-20.
- "MIT students seek to harness waste heat – MIT News Office". Web.mit.edu. 2008-07-24. Retrieved 2011-09-25.
-  Archived July 4, 2010, at the Wayback Machine.
- "Heating Plant". www.ndsu.edu. Retrieved 18 March 2018.
- "平成21年4月現在支部別熱供給事業者: The Japan Heat Service Utilities Associations 2009". Jdhc.or.jp. Archived from the original on 2011-10-07. Retrieved 2011-09-25.
- "Structure". Archived from the original on 2006-12-18. 080304 bbm.me.uk
- "Geothermie district heating scheme Southampton United Kingdom" (PDF). 080304 energie-cites.org
- Sabine Froning (Euroheat & Power): DHC/CHP/RES a smile for the environment, Kiev 2003 Archived February 25, 2009, at the Wayback Machine.
- "So heizt Deutschland heute". www.bmwi-energiewende.de. Retrieved 18 March 2018.
- "District Energy in France - Euroheat & Power". euroheat.org. 1 May 2017. Retrieved 18 March 2018.
|Wikimedia Commons has media related to District heating.|
- UK's Information Portal on Decentralised and District Energy
- District Energy Library
- Technical description of district heating and district cooling at Munich Airport, Germany
- Geothermal District Heating, Iceland
- Future Challenges for CHP in the UK and Continental Europe, Feb 2010 by F.Starr
- Max Fordham argues against use of CHP District Heating
- Energy Hub – EU funded FP7 Project – District heating, cooling and power aiming for 100% on-site renewable energy at Leuven, Belgium
- Advantages and Disadvantages of CHP district heating compared to heating and cooling from Heat Sharing Networks.
- A Balanced Energy Network integrates heat pumps, demand side response and distributed heat storage in a district heat sharing network.