This article has multiple issues. Please help improve it or discuss these issues on the talk page. (Learn how and when to remove these template messages)
A security alarm is a system designed to detect intrusion, such as unauthorized entry, into a building or other areas such as a home or school. Security alarms used in residential, commercial, industrial, and military properties protect against burglary (theft) or property damage, as well as personal protection against intruders. Security alerts in neighborhoods show a connection with diminished robbery. Car alarms likewise help protect vehicles and their contents. Prisons also use security systems for the control of inmates.
Some alarm systems serve a single purpose of burglary protection; combination systems provide fire and intrusion protection. Intrusion-alarm systems are combined with closed-circuit television surveillance (CCTV) systems to record intruders' activities and interface to access control systems for electrically locked doors. There are many types of security systems. Homeowners typically have small, self-contained noisemakers. These devices can also be complicated, multirole systems with computer monitoring and control. It may even include a two-way voice which allows communication between the panel and monitoring station.
The most basic alarm consists of at least one sensor to detect trespassers and an alerting device to indicate the intrusion. However, a typical premises security alarm employs the following components:
- Premises control unit (PCU), alarm control panel (ACP), or simply panel: The "brain" of the system; reads sensor inputs, tracks arm/disarm status, and signals intrusions. In a modern device, there are typically one or more computer circuit boards inside a metal enclosure. Many newer networks often use sealed plastic boxes out in the open. Some also have their control units built-in to the keypad or other human-machine interface.
- Sensors: Devices that detect intrusions. Sensors' locations are at the perimeter of the protected area, within it, or both. Sensors can detect intruders by different methods. For example, sensors can monitor doors and windows for openings or monitor unoccupied interiors for motions, sound, vibration, or other disturbances
- Alerting devices: These indicate an alarm condition. Most commonly, these are bells, sirens, also and or flashing lights. Alerting devices serve the dual purposes of warning occupants of intrusion and potentially scaring off burglars. These devices can also warn occupants of a fire or smoke condition
- Keypads: Small devices, typically wall-mounted, function as the human-machine interface to the system. In addition to buttons, keypads typically feature indicator lights, a small multi-character display, or both.
- Interconnections between components. Interconnections may consist of direct wiring to the control unit or wireless links with local power supplies.
In addition to the system itself, security alarms often offer a monitoring service. In the event of an alarm, the premises control unit contacts a central monitoring station. Operators at the station see the signal and take appropriate action, such as contacting property owners, notifying police, or dispatching private security forces. Such alerts transmit via dedicated alarm circuits, telephone lines, or the internet in many cases.
Hermetically sealed reed switchesEdit
The hermetically sealed reed switch is a common type of two-piece sensor. This switch operates with an electrically conductive reed switch that is either normally open or normally closed when under the influence of a magnetic field in respect to proximity to the second piece, which contains a magnet. When the magnet moves away from the reed switch, the reed switch either closes or opens, again based on whether the design is usually open or closed. This action coupled with an electric current (typically at 12V DC) allows an alarm control panel to detect a fault on that zone or circuit. These sensors are common, are found wired directly to an alarm control panel, or are typically found in wireless door or window contacts as sub-components.
Passive infrared detectorsEdit
The passive infrared (PIR) motion detector is one of the most common sensors found in household and small business environments. It offers affordable and reliable functionality. The term passive refers to the fact that the detector does not generate or radiate energy; it works entirely by detecting the heat energy given off by other objects.
Strictly speaking, PIR sensors do not detect motion; instead, they identify abrupt changes in temperature at a given point. As an intruder walks in front of the sensor, the temperature at that point will rise from room temperature to body temperature, and then back again. This quick change triggers the detection.
PIR sensors designed to be wall- or ceiling-mounted, come in various fields of view, from narrow-point detectors to 360-degree radar. PIRs require a power supply in addition to the detection signaling circuit.
The infrasound detector works by detecting infrasound, or sound waves at frequencies below 20 hertz. Sounds at those frequencies are inaudible to the human ear. Due to its inherent properties, infrasound can travel distances of many hundreds of kilometers. Infrasound signals can result from volcanic eruptions, earthquakes, gravity waves, opening and closing of doors, and forcing windows, to name a few.
The entire infrasound detection system consists of the following components: a speaker (infrasound sensor) as a microphone input, an order-frequency filter, an analog to digital (A/D) converter, and finally, an MCU used to analyze the recorded signal.
Each time a potential intruder tries to enter into a house, she or he tests whether it is closed and locked, uses tools on openings, or/and applies pressure, and therefore he or she creates low-frequency sound vibrations. Before the intruder breaks in, the infrasound detector automatically catches sight of the intruder's actions
The purpose of such a system is to detect burglars before they enter the house to avoid both theft and vandalism. The sensitivity is dependent on the size of a home and the presence of animals.
These active detectors transmit ultrasonic sound waves that are inaudible to humans using frequencies between 15 kHz and 75 kHz. The Doppler shift principle is the underlying method of operation which detects a change in frequency due to object motion. This detection occurs when the object must cause a change in the ultrasonic frequency to the receiver relative to the transmitting frequency.
The ultrasonic detector operates by the transmitter emitting an ultrasonic signal into the area to be protected. Solid objects (such as the surrounding floor, walls, and ceiling) reflect sound waves, which the receiver will detect. Because ultrasonic waves are transmitted through air, hard-surfaced objects tend to reflect most of the ultrasonic energy, while soft surfaces tend to absorb the most energy.
When the surfaces are stationary, the frequency of the waves detected by the receiver will be equal to the transmitted frequency. However, a change in frequency will occur as a result of the Doppler principle, when a person or object is moving towards or away from the detector. Such an event initiates an alarm signal. This technology is not active in many properties because many alarm professionals consider this obsolete.
This device emits microwaves from a transmitter and detects any reflected microwaves or reduction in beam intensity using a receiver. The transmitter and receiver are usually combined inside a single housing (monostatic) for indoor applications and separate housings (bistatic) for the protection of outdoor perimeters high-risk sites and critical infrastructures such as fuel storage, petrochemical facilities, military sites, civil and military airports, nuclear facilities and more. To reduce false alarms this type of detector is usually combined with a passive infrared detector, or Dual Tec brand or similar alarm. Compared to the monostatic, the bistatic units work over longer distances: typical distances for transmitter-receivers up to 200 m for X-band frequencies and up to 500 m for K-band frequencies.
Microwave detectors respond to a Doppler shift in the frequency of the reflected energy, by a phase shift, or by a sudden reduction of the level of received energy. Any of these effects may indicate motion of an intruder.
- Advantages: low cost, easy to install, invisible perimeter barrier. It is not affected by fog, rain, snow, sand storms, or wind.
- Disadvantages: May be affected by the presence of water dripping on the ground. Typically need a sterile clearance area to prevent partial blocking of the detection field.
The microwave generator is equipped with an antenna that allows it to concentrate the beam of electromagnetic waves in one preferred location and the beam is intercepted by the receiver, equipped with a similar antenna to the transmitter.
The graphical representation of the beam is similar to a cigar, and, when not disturbed, it runs between the transmitter and the receiver and generates a continuous signal. When an individual tries to cross this beam, it produces a disturbance that is caught by the receiver as a variation of amplitude of the received signal.
These barriers are immune to harsh weather, such as fog, heavy rain, snow and sandstorms: none of these atmospheric phenomena affect in any way the behaviour and the reliability of the microwave detection. Furthermore, the working temperature range of this technology goes from -35°C to +70°C.
Digital analysis of the signalEdit
The more recent and higher performance models of these detectors adopt a digital technology with “Fuzzy Logic” analysis of the signals. Those who use this generate a detection whether the intruder is rolling, crossing, crawling or moving very slow within the electromagnetic field. Thanks to this innovative technology, capable of targeting movements, the outcome is a reduction in false alarms. The ellipsoidal shape of the longitudinal section however does not allow a good detection capability close to the receiver or transmitter heads, so we identify these areas as dead zones. A solution to avoid this problem, when installing 2 or more barriers, is to cross the respective transmitter and receiver heads some meters from the respective heads or to use mono-head sensor to cover the above mentioned dead zones. 
Compact surveillance radarEdit
Compact surveillance radar emits microwaves from a transmitter and detects any reflected microwaves. They are similar to microwave detectors but can detect the precise location of intruders in areas extending over hundreds of acres. With the capability of measuring the range, angle, velocity, direction, and size of the target, a CSR can pinpoint a precise GPS coordinate of an intruder. This target information is typically displayed on a map, user interface or situational awareness software that defines geographical alert zones or geofences with different types of actions initiated depending on time of day and other factors. CSR is commonly used to protect outside the fence line of critical facilities such as electrical substations, power plants, dams, and bridges.
Photoelectric beam systems detect the presence of an intruder by transmitting invisible infrared light beams across an area, where these beams may be obstructed. To improve the detection surface area, the beams are often employed in stacks of two or more. However, if an intruder is aware of the technology's presence, it can be avoided. The technology can be an effective long-range detection system, if installed in stacks of three or more where the transmitters and receivers are staggered to create a fence-like barrier. Systems are available for both internal and external applications. To prevent a clandestine attack using a secondary light source being used to hold the detector in a sealed condition whilst an intruder passes through, most systems use and detect a modulated light source. - Advantages: low cost, easy to install. Require very little sterile clearance area to operate - Disadvantages: Affected by fog or very high luminosity. Position of the transmitter can be located with some cameras.
A glass-break detector may be used for internal perimeter building protection. Glass-break acoustic detectors are mounted in close proximity to the glass panes and listen for sound frequencies associated with glass breaking.
Seismic glass-break detectors, generally referred to as shock sensors, are different in that they are installed on the glass pane. When glass breaks it produces specific shock frequencies which travel through the glass and often through the window frame and the surrounding walls and ceiling. Typically, the most intense frequencies generated are between 3 and 5 kHz, depending on the type of glass and the presence of a plastic interlayer. Seismic glass-break detectors feel these shock frequencies and in turn generate an alarm condition.
Window foil is a less sophisticated, mostly outdated detection method that involves gluing a thin strip of conducting foil on the inside of the glass and putting low-power electric current through it. Breaking the glass is for all intents and purposes ensured to tear the foil and break the circuit.
Smoke, heat, and carbon monoxide detectorsEdit
Most systems can also be equipped with smoke, heat, and/or carbon monoxide detectors. These are also known as 24-hour zones (which are on at all times). Smoke and heat detectors protect from the risk of fire using different detection methods. Carbon monoxide detectors help protect from the risk of carbon monoxide poisoning. Although an intruder alarm panel may also have these detectors connected, it may not meet all the local fire code requirements of a fire alarm system.
Traditional smoke detectors are technically ionization smoke detectors which create an electric current between two metal plates, which sound an alarm when disrupted by smoke entering the chamber. Ionization smoke alarms can quickly detect the small amounts of smoke produced by fast-flaming fires, such as cooking fires or those fueled by paper or flammable liquids. A newer, and perhaps safer, type is a photoelectric smoke detector. It contains a light source in a light-sensitive electric sensor, which is positioned at a 90-degree angle to the sensor. Normally, light from the light source shoots straight across and misses the sensor. When smoke enters the chamber, it scatters the light, which then hits the sensor and triggers the alarm. Photoelectric smoke detectors typically respond faster to a fire in its early, smoldering stage – before the source of the fire bursts into flames.
Motion sensors are devices that use various forms of technology to detect movement. The technology typically found in motion sensors to trigger an alarm includes infrared, ultrasonic, vibration and contact. Dual technology sensors combine two or more forms of detection in order to reduce false alarms as each method has its advantages and disadvantages. Traditionally motion sensors are an integral part of a home security system. These devices are typically installed to cover a large area as they commonly cover up to 40 ft. with a 135° field of vision.
Driveway alarm systems can be combined with most security and automation systems. They are designed to alert residents to unexpected visitors, intruders, or deliveries arriving at the property. They come in magnetic and infrared motion sensing options. Driveway alarms can also be purchased in hard-wired and wireless systems. They are common in rural security systems as well as for commercial applications.
Electro-mechanical (shaker) sensorsEdit
These electro-mechanical devices are mounted on barriers and are used primarily to detect an attack on the structure itself. The technology relies on an unstable mechanical configuration that forms part of the electrical circuit. When movement or vibration occurs, the unstable portion of the circuit moves and breaks the current flow, which produces an alarm. The medium transmitting the vibration must be correctly selected for the specific sensor as they are best suited to different types of structures and configurations. This technology is gradually being replaced by intelligent digital accelerometer-based systems.
- Advantages: Low-cost and easily installed on existing fences.
- Disadvantages: Must be fence-mounted. Being mechanical in nature, the system is unable to analyze differences in the pattern of vibrations (for example, the difference between gusts of wind and a person climbing the fence).
Ferrous metal detectorsEdit
Change in the local magnetic field due to the presence of ferrous metals induces a current in the buried sensors (buried cables or discrete sensors) which are analyzed by the system. If the change exceeds a predetermined threshold, an alarm is generated. This type of sensor can be used to detect intruders carrying substantial amounts of metal, such as a firearm, making it ideally suited for anti-poaching applications.
Sometimes referred to as E-field, this volumetric sensor uses Electric field proximity sensing and can be installed on buildings, perimeters, fences, and walls. It also has the ability to be installed free-standing on dedicated poles. The system uses an electromagnetic field generator powering one wire, with another sensing wire running parallel to it. The sensing wire is connected to a signal processor that analyses:
- amplitude change (mass of intruder),
- rate change (movement of intruder),
- preset disturbance time (time the intruder is in the pattern).
These items define the characteristics of an intruder and when all three are detected simultaneously, an alarm signal is generated.
The barrier can provide vertical protection from the ground to the height of the mounting posts (typically 4–6 meters of height), depending on the number of sensor wires installed. It is usually configured in zones of about 200 metre lengths.
- Advantage: High-security (difficult to defeat), high vertical detection field.
- Disadvantages: Expensive, short zones which mean more electronics (and thus a higher cost).
Microphonic systems vary in design (for example, time-domain reflectrometer or piezo-electric) but each is generally based on the detection of an intruder attempting to cut or climb over a fence. Usually the microphonic detection systems are installed as sensor cables attached to rigid chain-wire fences, however some specialized versions of these systems can also be installed as buried systems underground. Depending on the version selected, it can be sensitive to different frequencies or levels of noise or vibration. The system is based on coaxial or electro-magnetic sensor cable with the controller having the ability to differentiate between signals from the cable or chain-wire being cut, an intruder climbing the fence, or bad weather conditions.
The systems are designed to detect and analyze incoming electronic signals received from the sensor cable, and then to generate alarms from signals which exceed pre-set conditions. The systems have adjustable electronics to permit installers to change the sensitivity of the alarm detectors to the suit specific environmental conditions. The tuning of the system is usually accomplished during commissioning of the detection devices.
- Advantages: Relatively inexpensive compared to other systems and easy to install.
- Disadvantage: Older systems may have a high rate of false alarms caused by wind and other distances, although newer systems use DSP (digital signal processing) to process the signal and greatly reduce false alarms in some cases.
Taut wire fence systemsEdit
A taut wire perimeter security system is basically an independent screen of tensioned tripwires usually mounted on a fence or wall. Alternatively, the screen can be made so thick that there is no need for a supporting chain-wire fence. These systems are designed to detect any physical attempt to penetrate the barrier. Taut wire systems can operate with a variety of switches or detectors that sense movement at each end of the tense wires. These switches or detectors can be a simple mechanical contact, static force transducer or an electronic strain gauge. Unwanted alarms caused by birds and other animals can be avoided by adjusting the sensors to ignore objects that exert small amounts of pressure on the wires. This type of system is vulnerable to intruders digging under the fence. A concrete footing directly below the fence is installed to prevent this type of attack.
- Advantages: low rate of false alarms, very reliable sensors, and high rate of detection.
- Disadvantages: very expensive and complicated to install.
Fiber optic cableEdit
A fiber-optic cable can be used to detect intruders by measuring the difference in the amount of light sent through the fiber core. A variety of fiber optic sensing technologies may be used, including Rayleigh scattering or interferometry, If the cable is disturbed, the light will be changed and the intrusion detected. The cable can be attached directly to a chain-wire fence or bonded into a barbed steel tape that is used to protect the tops of walls and fences. This type of barbed tape provides a good physical deterrent as well as giving an immediate alarm if the tape is cut or severely distorted.
- Advantages: Being cable-based, very similar to the microphonic system and easy to install. Allow to cover large perimeters (few tens of Km).
- Disadvantage: Typically performs in a manner similar to microphonic-based systems but at a higher cost and complexity due to the use of fiberoptic technology.
Ported coaxial cableEdit
This system employs an electro-magnetic field disturbance principle based on two unshielded (or 'leaky') coaxial cables buried approximately 30 cm (1 ft.) deep and 1 m (3 ft.) apart. The transmitter emits continuous Radio Frequency (RF) energy along one cable and the energy is received by the other cable. When the change in field strength weakens due to the presence of an object and reaches a pre-set lower threshold, an alarm condition is generated. The system is covert after installation. Care must be taken to ensure the surrounding soil offers good drainage in order to avoid nuisance alarms.
- Advantage: concealed as a buried form.
- Disadvantages: can be affected by RF noise, difficult to install.
Security electric fenceEdit
Security electric fences consist of wires that carry pulses of electric current to provide a non-lethal shock to deter potential intruders. Tampering with the fence also results in an alarm that is logged by the security electric fence energiser, and can also trigger a siren, strobe, and/or notifications to a control room or directly to the owner via email or phone. In practical terms, security electric fences are a type of sensor array that acts as a (or part of a) physical barrier, a psychological deterrent to potential intruders, and as part of a security alarm system.
- Advantages: less expensive than many other methods, less likely to give false alarms than many other alternative perimeter security methods, and highest psychological deterrent of all methods.
- Disadvantage: potential for unintended shock.
Wired, wireless, and hybrid systemsEdit
The trigger signal from every sensor is transmitted to one or more control units either through wires or wireless means (radio, line carrier, infrared). Wired systems are convenient when sensors (such as PIRs, smoke detectors, etc.) require external power to operate correctly; however, they may be more costly to install. Entry-level wired systems utilize a star network topology, where the panel is at the center logically, and all devices home run their line wires back to the panel. More complex panels use a Bus network topology where the wire basically is a data loop around the perimeter of the facility, and has drops for the sensor devices which must include a unique device identifier integrated into the sensor device itself (e.g. id. biscuit). Wired systems also have the advantage, if wired properly for example by dual loop, of being tamper-evident.
Wireless systems, on the other hand, often use battery-powered transmitters which are easier to install and have less expensive start-up costs, but may fail if the batteries are not maintained. Depending on distance and construction materials, one or more wireless repeaters may be required to bring the signal to the alarm panel reliably. A wireless system can be moved to a new home easily, an advantage for those who rent or who move frequently. The more important wireless connection for security is the one between the control panel and the monitoring station. Wireless monitoring of the alarm system protects against a burglar cutting a cable or from failures of an internet provider. This full wireless setup is commonly referred to as 100% wireless.
Hybrid systems use both wired and wireless sensors to achieve the benefits of both. Transmitters can also be connected through the premises' electrical circuits to transmit coded signals to the control unit (line carrier). The control unit usually has a separate channel or zone for burglar and fire sensors, and better systems have a separate zone for every different sensor, as well as internal trouble indicators (mains power loss, low battery, broken wire, etc.).
Alarm connection and monitoringEdit
Depending upon the application, the alarm output may be local, remote or a combination. Local alarms do not include monitoring, though may include indoor and/or outdoor sounders (e.g. motorized bell or electronic siren) and lights (e.g. strobe light) which may be useful for signaling an evacuation notice for people during fire alarms, or where one hopes to scare off an amateur burglar quickly. However, with the widespread use of alarm systems (especially in cars), false alarms are very frequent and many urbanites tend to ignore alarms rather than investigating, let alone contacting the necessary authorities. In short, there may be no response at all. In rural areas where nobody may hear the fire bell or burglar siren, lights or sounds may not make much difference, as the nearest emergency responders may arrive too late to avoid losses.
Remote alarm systems are used to connect the control unit to a predetermined monitor of some sort, and they come in many different configurations. High-end systems connect to a central station or first responder (e.g. police/fire/medical) via a direct phone wire, a cellular network, a radio network (i.e. GPRS/GSM), or an IP path. In the case of a dual signaling system two of these options are utilized simultaneously. The alarm monitoring includes not only the sensors, but also the communication transmitter itself. While direct phone circuits are still available in some areas from phone companies, because of their high cost and the advent of dual signaling with its comparatively lower cost they are becoming uncommon. Direct connections are now most usually seen only in federal, state, and local government buildings, or on a school campus that has a dedicated security, police, fire, or emergency medical department (in the UK communication is only possible to an alarm receiving centre – communication directly to the emergency services is not permitted).
More typical systems incorporate a digital cellular communication unit that will contact the central station (or some other location) via the Public Switched Telephone Network (PSTN) and raise the alarm, either with a synthesized voice or increasingly via an encoded message string that the central station decodes. These may connect to the regular phone system on the system side of the demarcation point, but typically connect on the customer side ahead of all phones within the monitored premises so that the alarm system can seize the line by cutting-off any active calls and call the monitoring company if needed. A dual signaling system would raise the alarm wirelessly via a radio path (GPRS/GSM) or cellular path using the phone line or broadband line as a back-up overcoming any compromise to the phone line. Encoders can be programmed to indicate which specific sensor was triggered, and monitors can show the physical location (or "zone") of the sensor on a list or even a map of the protected premises, which can make the resulting response more effective. For example, a heat sensor alarm, coupled with a flame detector in the same area is a more reliable indication of an actual fire than just one or the other sensor indication by itself.
Many alarm panels are equipped with a backup communication path for use when the primary PSTN circuit is not functioning. The redundant dialer may be connected to a second communication path, or a specialized encoded cellular phone, radio, or internet interface device to bypass the PSTN entirely, to thwart intentional tampering with the phone lines. Just the fact that someone tampered with the line could trigger a supervisory alarm via the radio network, giving early warning of an imminent problem (e.g. arson). In some cases a remote building may not have PSTN phone service, and the cost of trenching and running a direct line may be prohibitive. It is possible to use a wireless cellular or radio device as the primary communication method.
In the UK the most popular solution of this kind is similar in principle to the above but with the primary and back up paths reversed. Utilizing a radio path (GPRS/GSM) as the primary signaling path is not only quicker than PSTN but also allows huge cost savings as unlimited amounts of data can be sent at no extra expense.
Broadband alarm monitoringEdit
Increasing deployment of voice over IP technology (VoIP) is driving the adoption of broadband signaling for alarm reporting. Many sites requiring alarm installations no longer have conventional telephone lines (POTS), and alarm panels with conventional telephone dialer capability do not work reliably over some types of VoIP service.
Dial-up analogue alarm panels or systems with serial/parallel data ports may be migrated to broadband through the addition of an alarm server device which converts telephone signaling signals or data port traffic to IP messages suitable for broadband transmission. But the direct use of VoIP (POTS port on premises terminal) to transport analogue alarms without an alarm server device is problematic as the audio codecs used throughout the entire network transmission path cannot guarantee a suitable level of reliability or quality of service acceptable for the application.
In response to the changing public communications network and new alarm systems often can use broadband signaling as a method of alarm transmission, and manufacturers are including IP reporting capability directly in their alarm panel products. When the Internet is used as a primary signaling method for critical security and life safety applications, frequent supervision messages are configured to overcome concerns about backup power for network equipment and signal delivery time. But for typical applications, connectivity concerns are controlled by normal supervision messages, sent daily or weekly.
Various IP Alarm transmission protocols exist but most in use today are proprietary. Just as the formats used for conventional telephone reporting were standardized and published, broadband signaling for alarm reporting is being standardized today. In 2007, US alarm manufacturers developed an open standard called DC-09. This standard has been accepted as an American National Standard, and is published as ANSI/SIA DC-09-2007. [ref: ANSI/SIA DC-09-2007] without The protocol provides an encoding scheme and transport mechanism to carry data from 17 previously defined alarm protocols, including the latest Contact ID, SIA DC-03 and SIA 2000 protocols. [ref: ANSI/SIA DC-07-2001.04] Several manufacturers of panels and receivers are reported to be developing or have released support for DC-09.
Radio alarm dual signalingEdit
Dual signaling is a method of alarm transmission that uses a mobile phone network and a telephone and/or IP path to transmit intruder, fire and personal attack signals at high speed from the protected premises to an Alarm Receiving Centre (ARC). It most commonly uses GPRS or GSM, a high-speed signaling technology used to send and receive ‘packets’ of data, with a telephone line in addition. The option of IP is not used as frequently due to issues with installation and configuration as a high level of I.T expertise is often required in addition to alarm installation knowledge.
A dual signaling communication device is attached to a control panel on a security installation and is the component that transmits the alarm to the ARC. It can do this in a number of different ways, via the GPRS radio path, via the GSM radio path or via the telephone line/or IP if that has been chosen. These multiple signaling paths are all present and live at the same time backing each other up to minimize exposure of the property to intruders. Should one fail there is always one form of back up and depending on the manufacturer chosen up to three paths working simultaneously at any one time. Prior to the availability of dual signaling systems, police and keyholders were often called out to the premises because of an alarm signal on the telephone path only to discover that it was a network fault and not a genuine alarm
Dual paths allow distinction between hardware failures and a genuine attack on the alarm. This helps eliminate false alarms and unnecessary responses. Dual signaling has helped considerably with the restoration of Police response as in an instance where a phone line is cut as the dual signaling device can continue to send alarm calls via one of its alternative paths either confirming or denying the alarm from the initial path.
In the UK, CSL DualCom Ltd pioneered dual signaling in 1996. In doing so, the company offered the first credible alternative to existing alarm signaling while setting the current standard for professional dual path security monitoring. Dual signaling is now firmly regarded as the standard format for alarm signaling and is duly specified by all of the leading insurance companies.
Listen-in alarm monitoringEdit
Monitored alarms and speaker phones allow for the central station to speak with the homeowner or intruder. This may be beneficial to the owner for medical emergencies. For actual break-ins, the speaker phones allow the central station to urge the intruder to cease and desist as response units have been dispatched. Listen-in alarm monitoring is also known as Immediate Audio-Response monitoring or Speaking Alarm Systems in the UK.
Alarm monitoring servicesEdit
The list of services to be monitored at a Central Station has expanded over the past few years to include: Access Control; CCTV Monitoring; Alarm Verification; Environmental Monitoring; Intrusion Alarm Monitoring; Fire Alarm & Sprinkler Monitoring; Critical Condition Monitoring; Medical Response Monitoring; Elevator Telephone Monitoring; Hold-Up or Panic Alarm Monitoring; Duress Monitoring; Auto Dialer tests; Open & Close Signal Supervision & Reporting; Exception Reports; and PIN or Passcode Management. Increasingly, the Central Stations are making this information available directly to end users via the internet and a secure log-on to view and create custom reports on these events themselves.
Depending upon the zone triggered, number and sequence of zones, time of day, and other factors, the alarm monitoring center may automatically initiate various actions. Central station operators might be instructed to call emergency services immediately, or to first call the protected premises or property manager to try to determine if the alarm is genuine. Operators could also start calling a list of phone numbers provided by the customer to contact someone to go check on the protected premises. Some zones may trigger a call to the local heating oil company to go check on the system, or a call to the owner with details of which room may be getting flooded. Some alarm systems are tied to video surveillance systems so that current video of the intrusion area can be instantly displayed on a remote monitor, not to mention recorded.
Some alarm systems use real-time audio and video monitoring technology to verify the legitimacy of an alarm. In some municipalities around the United States, this type of alarm verification allows the property it is protecting to be placed on a "verified response" list, allowing for quicker and safer police responses.
The first video home security system was patented on December 2, 1969 to inventor Marie Brown. The system used television surveillance.
Access control and bypass codesEdit
To be useful, an intrusion alarm system is deactivated or reconfigured when authorized personnel are present. Authorization may be indicated in any number of ways, often with keys or codes used at the control panel or a remote panel near an entry. High-security alarms may require multiple codes, or a fingerprint, badge, hand-geometry, retinal scan, encrypted-response generator, and other means that are deemed sufficiently secure for the purpose.
Failed authorizations should result in an alarm or at least a timed lockout to prevent experimenting with possible codes. Some systems can be configured to permit deactivation of individual sensors or groups. Others can also be programmed to bypass or ignore individual sensors (once or multiple times) and leave the remainder of the system armed. This feature is useful for permitting a single door to be opened and closed before the alarm is armed, or to permit a person to leave, but not return. High-end systems allow multiple access codes, and may even permit them to be used only once, or on particular days, or only in combination with other users' codes (i.e., escorted). In any case, a remote monitoring center should arrange an oral code to be provided by an authorized person in case of false alarms, so the monitoring center can be assured that a further alarm response is unnecessary. As with access codes, there can also be a hierarchy of oral codes, say, for furnace repairperson to enter the kitchen and basement sensor areas but not the silver vault in the pantry. There are also systems that permit a duress code to be entered and silence the local alarm, but still trigger the remote alarm to summon the police to a robbery.
Fire sensors can be isolated, meaning that when triggered, they will not trigger the main alarm network. This is important when smoke and heat is intentionally produced. The owners of buildings can be fined for generating false alarms that waste the time of emergency personnel.
False and absent alarmsEdit
System reliability and user error are the cause of most false alarms, sometimes called "nuisance alarms." False alarms can be very costly to local governments, local law enforcement, security system users and members of local communities. In 2007, the Department of Justice reported that in just one year, false alarms cost local municipalities and their constituents at least $1.8 billion.
In many municipalities across the United States, policies have been adopted to fine home and business owners for multiple false alarm activations from their security system. If multiple false alarms from the same property persist, that property could even be added to a "no response" list, which bars police dispatch to the property except in the event of verified emergency. Approximately 1% of police alarm calls actually involve a crime. Nuisance alarms occur when an unintended event evokes an alarm status by an otherwise properly working alarm system. A false alarm also occurs when there is an alarm system malfunction that results in an alarm state. In all three circumstances, the source of the problem should be immediately found and fixed, so that responders will not lose confidence in the alarm reports. It is easier to know when there are false alarms, because the system is designed to react to that condition. Failure alarms are more troublesome because they usually require periodic testing to make sure the sensors are working and that the correct signals are getting through to the monitor. Some systems are designed to detect problems internally, such as low or dead batteries, loose connections, phone circuit trouble, etc. While earlier nuisance alarms could be set off by small disturbances, like insects or pets, newer model alarms have technology to measure the size/weight of the object causing the disturbance, and thus are able to decide how serious the threat is, which is especially useful in burglar alarms.
False alarm reductionEdit
Many municipalities across the United States require alarm verification before police are dispatched. Under this approach, alarm monitoring companies must verify the legitimacy of alarms (except holdup, duress, and panic alarms) before calling the police. Verified response typically involves visual on-scene verification of a break-in, or remote audio or video verification.
Home and business owners can now choose a new type of keypad control panel designed to help reduce false alarms.
Based on a standard called CP-01-2000, developed by the American National Standards Institute and Security Industry Association, the new generation of keypad control panels takes aim at user error by building in extra precautions that minimize unwarranted dispatch of emergency responders.
Some of the features of CP-01 keypads include a progress annunciation function that emits a different sound during the last 10 seconds of delay, which hastens exit from the premises. Also, the exit time doubles if the user disables the pre-warning feature.
Other "rules" address failure to exit premises, which results in arming all zones in Stay Mode and a one-time, automatic restart of exit delay. However, if there is an exit error, an immediate local alarm will sound.
Audio and video verificationEdit
Alarms that utilize audio, video, or combination of both audio and video verification technology give security companies, dispatchers, police officers, and property managers more reliable data to assess the threat level of a triggered alarm.
Audio and video verification techniques use microphones and cameras to record audio frequencies, video signals, or image snapshots. The source audio and video streams are sent over a communication link, usually an Internet protocol (IP) network, to the central station where monitors retrieve the images through proprietary software. The information is then relayed to law enforcement and recorded to an event file, which can be used to plan a more strategical and tactical approach of a property, and later as prosecution evidence.
An example of how this system works is when a passive infrared or other sensor is triggered a designated number of video frames from before and after the event is sent to the central station.
A second video solution can be incorporated into a standard panel, which sends the central station an alarm. When a signal is received, a trained monitoring professional accesses the on-site digital video recorder (DVR) through an IP link to determine the cause of the activation. For this type of system, the camera input to the DVR reflects the alarm panel's zones and partitioning, which allows personnel to look for an alarm source in multiple areas.
The United States Department of Justice states that legislation requiring alarm companies to verify the legitimacy of an alarm, before contacting law enforcement (commonly known as "verified response") is the most effective way to reduce false burglar alarms. The Department of Justice considers audio, video, or an eye-witness account as verification for the legitimacy of a burglar alarm.
Cross-zoning is a strategy that does not require a new keypad. Using multiple sensors to monitor activity in one area, software analyses input from all the sources. For example, if a motion detector trips in one area, the signal is recorded and the central-station monitor notifies the customer. A second alarm signal—received in an adjacent zone within a short time—is the confirmation the central-station monitor needs to request a dispatch immediately. This builds in increased protection and a fail-safe should a door blow open or a bird rattle an exterior window.
Enhanced call verificationEdit
Enhanced call verification (ECV) helps reduce false dispatches 25–50% while still protecting citizens, and is mandated in several US jurisdictions, although the alarm industry has successfully opposed it in others. ECV requires central station personnel to attempt to verify the alarm activation by making a minimum of two phone calls to two different responsible party telephone numbers before dispatching law enforcement to the scene.
The first alarm-verification call goes to the location the alarm originated. If contact with a person is not made, a second call is placed to a different number. The secondary number, best practices dictate, should be to a telephone that is answered even after hours, preferably a cellular phone of a decision maker authorized to request or bypass emergency response.
ECV, as it cannot confirm an actual intrusion event and will not prompt a priority law enforcement dispatch, is not considered true alarm verification by the security industry.
Some insurance companies and local agencies require that alarm systems be installed to code or be certified by an independent third party. The alarm system is required to have a maintenance check carried out every 6 – 12 months (in the UK, 'Audible Only' intruder alarm systems require a routine service visit once every 12 months and monitored intruder alarm systems require a check twice in every 12-month period) to ensure all internal components, sensors and PSUs are functioning correctly. In the past, this would require an alarm service engineer to attend site and carry the checks out. With the use of the Internet or radio path and a compatible IP/radio transmitting device (at the alarmed premises), some checks can now be carried out remotely from the central station.
- "NASA Langley Researchers Nab Invention of the Year for Infrasound Detection System". www.nasa.gov. 2014-07-25.
- Chilo & Lindblad 2008.
- The National Institute of Justice (1998). "Perimeter Security Sensor Technologies Handbook" (PDF). Defense Advance Research Project Agency (DARPA): NIJ: 2.12–2.13.
- "Guide to Perimeter Intrusion Detection Systems (PIDS)". Centre for the Protection of National Infrastructure (CPNI). No. 05/12: 24–38. 2012.
- De Astis, Vincenzo; Gasparini, Bruno (2019). Security technology handbook. Milano: Assosicurezza. pp. 100–102.
- "Guide to Perimeter Intrusion Detection Systems (PIDS)". CPNI - Centre for the Protection of National Infrastructure. No. 05/12: 24–38. 2012.
- "Perimeter Intrusion Alarm Systems" (PDF). U.S. Nuclear Regulatory Commission. 1997. Retrieved 14 December 2020.
- Trivedi, Bijal (14 May 2007). "Hunting Poachers Remotely". MIT Technology Review. Retrieved 26 October 2020. (subscription required)
- Chen & Young 1984.
- "Bowmark Capital backs £32 million MBO of CSL DualCom". IFSEC Global. Informa Markets. 12 January 2012. Retrieved 14 December 2020.
- Sampson, Rana (2011), False Burglar Alarms 2nd Edition (PDF), US Department of Justice / Office of Community Oriented Policing Services, ISBN 978-1-932582-04-8, archived from the original (PDF) on 2014-08-14
- Harrelson, Chuck (2013-09-30), Audio Verification Equals More Apprehensions, EH Publishing, retrieved May 17, 2014
- Chilo, José; Lindblad, Thomas (2008). "Wireless data acquisition system using Bluetooth technology for infrasonic records". Computing. 7 (2): 18–21. S2CID 109116579.
- Lee, Seungmug; Wilson, Harry (2013-04-01). "Spatial impact of burglar alarms on the decline of residential burglary". Security Journal. 26 (2): 180–198. doi:10.1057/sj.2012.8. ISSN 0955-1662. S2CID 154914584.
- Chen, Pin-Wei; Young, Gregory (December 1984). "Ported coax intrusion detection sensor". IEEE Transactions on Antennas and Propagation. 32 (12): 1313–1317. Bibcode:1984ITAP...32.1313C. doi:10.1109/TAP.1984.1143256. ISSN 1558-2221.
- Aii, N. Clifton. "Broadband CSV, XML Alarm data Standards" Auckland NZ, (2002)
- US patent 6297844, Nichani, Sanjay; Schatz, David A. & Shillman, Robert Joel, "Video safety curtain", published 2 October 2001, assigned to Cognex Corporation
- Trimmer, H.William (1999). Understanding and Servicing Alarm Systems (3rd ed.). Boston: Butterworth-Heinemann. ISBN 9780750672061. (registration required)
- Walker, Philip (2005). Electronic security systems: reducing false alarms. Oxford: Newnes. ISBN 9780750635431. (registration required)
- Weber, Thad L. (1985). Alarm systems and theft prevention (2nd ed.). Boston: Butterworth. OCLC 916164434. (registration required)
- "Wolf guard alarm system" China CN, (1998)