# Draft:Performance of AC Transmission Lines

Comment: Please do not use Wikipedia as a syllabus notes site for your IIT course. AngusWOOF (barksniff) 14:32, 22 July 2019 (UTC)

Comment: Wikipedia is not a textbook on Transmission line theory AngusWOOF (barksniff) 08:53, 20 July 2019 (UTC)

Comment: This reads like it comes from a textbook, full of formulas and such, and covers topics already covered in Wikipedia AngusWOOF (barksniff) 08:52, 20 July 2019 (UTC)

500 kV Three-phase electric power Transmission Lines at Grand Coulee Dam

Electric power transmission is the bulk movement of electrical energy from a generating site, such as a power plant, to an electrical substation. The interconnected lines which facilitate this movement are known as a transmission network. This is distinct from the local wiring between high-voltage substations and customers, which is typically referred to as electric power distribution. The combined transmission and distribution network is known as the "power grid" in North America, or just "the grid". In the United Kingdom, India, Tanzania, Myanmar, Malaysia and New Zealand, the network is known as the "National Grid".

Historically, transmission and distribution lines were owned by the same company, but starting in the 1990s, many countries have liberalized the regulation of the electricity market in ways that have led to the separation of the electricity transmission business from the distribution business..:[1]

## Overview

A transmission line is a set of electrical conductors carrying an electrical signal from one place to another. Coaxial cable and twisted pair cable are examples. Transmission line is capable of transmitting electrical power from one place to another. In many electric circuits, the length of the wires connecting the components can for the most part be ignored. That is, the voltage on the wire at a given time can be assumed to be the same at all points. However, when the voltage changes in a time interval comparable to the time it takes for the signal to travel down the wire, the length becomes important and the wire must be treated as a transmission line. Stated another way, the length of the wire is important when the signal includes frequency components with corresponding wavelengths comparable to or less than the length of the wire. So far transmission lines are categorized and defined in many ways. Few approaches of modeling have also being done by different methods. Most of them are mathematical and assumed circuit based models.

Basically transmission can be of two types :

• HVDC Transmission (High Voltage Direct Current transmission)
• HVAC Transmission (High Voltage Direct Current Transmission)

### HVDC transmission

High-voltage direct current (HVDC) is used to transmit large amounts of power over long distances or for interconnections between asynchronous grids. When electrical energy is to be transmitted over very long distances, the power lost in AC transmission becomes appreciable and it is less expensive to use direct current instead of alternating current[2]. For a very long transmission line, these lower losses (and reduced construction cost of a DC line) can offset the additional cost of the required converter stations at each end.In DC transmission line, the mercury arc rectifier converts the alternating current into the DC. The DC transmission line transmits the bulk power over long distance. At the consumer ends the thyratron converts the DC into the AC.

### HVAC transmission

The AC transmission line is used for transmitting the bulk of the power generation end to the consumer end. The power is generated in the generating station. The transmission line transmits the power from generation to the consumer end. High-voltage power transmission allows for lesser resistive losses over long distances in the wiring. This efficiency of high voltage transmission allows for the transmission of a larger proportion of the generated power to the substations and in turn to the loads, translating to operational cost savings. The power is transmitted from one end to another with the help of step-up and step down transformer. Most transmission lines are high-voltage three-phase alternating current (AC), although single phase AC is sometimes used in railway electrification systems. Electricity is transmitted at high voltages (115 kV or above) to reduce the energy loss which occurs in long-distance transmission.

Power is usually transmitted through overhead power lines. Underground power transmission has a significantly higher installation cost and greater operational limitations, but reduced maintenance costs. Underground transmission is sometimes used in urban areas or environmentally sensitive locations.

## Terminologies

### Lossless Line

The lossless line approximation is the least accurate model; it is often used on short lines when the inductance of the line is much greater than its resistance. For this approximation, the voltage and current are identical at the sending and receiving ends.

The characteristic impedance is pure real, which means resistive for that impedance, and it is often called surge impedance for a lossless line. When lossless line is terminated by surge impedance, there is no voltage drop. Though the phase angles of voltage and current are rotated, the magnitudes of voltage and current remain constant along the length of the line. For load > SIL, the voltage will drop from sending end and the line will “consume” VARs. For load < SIL, the voltage will increase from sending end, and the line will “generate” VARs.

### Power factor

In electrical engineering, the power factor of an AC electrical power system is defined as the ratio of the real power absorbed by the load to the apparent power flowing in the circuit, and is a dimensionless number in the closed interval of −1 to 1. A power factor of less than one indicates the voltage and current are not in phase, reducing the instantaneous product of the two. Real power is the instantaneous product of voltage and current and represents the capacity of the electricity for performing work. Apparent power is the average product of current and voltage. Due to energy stored in the load and returned to the source, or due to a non-linear load that distorts the wave shape of the current drawn from the source, the apparent power may be greater than the real power. A negative power factor occurs when the device (which is normally the load) generates power, which then flows back towards the source.

In an electric power system, a load with a low power factor draws more current than a load with a high power factor for the same amount of useful power transferred. The higher currents increase the energy lost in the distribution system, and require larger wires and other equipment. Because of the costs of larger equipment and wasted energy, electrical utilities will usually charge a higher cost to industrial or commercial customers where there is a low power factor.

Power-factor correction increases the power factor of a load, improving efficiency for the distribution system to which it is attached. Linear loads with low power factor (such as induction motors) can be corrected with a passive network of capacitors or inductors. Non-linear loads, such as rectifiers, distort the current drawn from the system. In such cases, active or passive power factor correction may be used to counteract the distortion and raise the power factor. The devices for correction of the power factor may be at a central substation, spread out over a distribution system, or built into power-consuming equipment.

### Surge Impedance

The characteristic impedance or surge impedance (usually written Z0) of a uniform transmission line is the ratio of the amplitudes of voltage and current of a single wave propagating along the line; that is, a wave travelling in one direction in the absence of reflections in the other direction. Alternatively and equivalently it can be defined as the input impedance of a transmission line when its length is infinite. Characteristic impedance is determined by the geometry and materials of the transmission line and, for a uniform line, is not dependent on its length. The SI unit of characteristic impedance is Ohm (Ώ)

Surge impedance determines the loading capability of line and reflection coefficient of the current or voltage propagating waves. ${\displaystyle Z_{0}={\sqrt {\frac {L}{C}}}}$

Where,

Z0 = Characteristic Impedance of the Line L = Inductance per unit length of the Line C = Capacitance per unit length of the Line

### Line Parameters

The transmission line has mainly four parameters, resistance, inductance, and capacitance and shunt conductance. These parameters are uniformly distributed along the line. Hence, it is also called the distributed parameter of the transmission line.

### Ferranti Effect

In electrical engineering, the Ferranti effect is the increase in voltage occurring at the receiving end of a very long (> 20 km) AC electric power transmission line, relative to the voltage at the sending end, when the load is very small, or no load is connected. It can be stated as a factor, or as a percent increase:..[3]

The capacitive line charging current produces a voltage drop across the line inductance that is in-phase with the sending-end voltage, assuming negligible line resistance. Therefore, both line inductance and capacitance are responsible for this phenomenon. This can be analysed by considering the line as a transmission line where the source impedance is lower than the load impedance (unterminated). The effect is similar to an electrically short version of the quarter-wave impedance transformer, but with smaller voltage transformation.

The Ferranti effect is more pronounced the longer the line and the higher the voltage applied.[4] The relative voltage rise is proportional to the square of the line length and the square of frequency.[5]

The Ferranti effect is much more pronounced in underground cables, even in short lengths, because of their high capacitance per unit length, and lower electrical impedance.

### Corona Discharge

A corona discharge is an electrical discharge brought on by the ionization of a fluid such as air surrounding a conductor that is electrically charged. Spontaneous corona discharges occur naturally in high-voltage systems unless care is taken to limit the electric field strength. A corona will occur when the strength of the electric field (potential gradient) around a conductor is high enough to form a conductive region, but not high enough to cause electrical breakdown or arcing to nearby objects. It is often seen as a bluish (or another color) glow in the air adjacent to pointed metal conductors carrying high voltages, and emits light by the same property as a gas discharge lamp.

In many high voltage applications, corona is an unwanted side effect. Corona discharge from high voltage electric power transmission lines constitutes an economically significant waste of energy. Corona discharges are suppressed by improved insulation, corona rings, and making high voltage electrodes in smooth rounded shapes.

### ABCD Parameters

A,B,C,D are the constants also known as the transmission parameters or chain parameters. These parameters are used for the analysis of an electrical network. It is also used for determining the performance of input, output voltage and current of the transmission network.

### Attenuation Constant

The real part of the propagation constant is the attenuation constant and is denoted by Greek lowercase letter α (alpha). It causes signal amplitude to decrease along a transmission line.

### Phase Constant

The imaginary part of the propagation constant is the phase constant and is denoted by Greek lowercase letter β (beta). It causes signal phase to shift along a transmission line. Generally denoted in radians per meter (rad/m).

### Propagation Constant

The propagation constant of sinusoidal electromagnetic wave is a measure of the change undergone by the amplitude and phase of the wave as it propagates in a given direction. The quantity being measured can be the voltage, the current in a circuit, or a field vector such as electric field strength or flux density. The propagation constant itself measures the change per unit length, but it is otherwise dimensionless. In the context of two-port networks and their cascades, propagation constant measures the change undergone by the source quantity as it propagates from one port to the next.

the propagation constant is denoted by Greek lowercase letter γ (gamma), and γ = α + jβ

### Voltage Regulation

Voltage regulation is a measure of change in the voltage magnitude between the sending and receiving end of a component, such as a transmission or distribution line. It is given in percentage for different lines.

Mathematically, voltage regulation is given by,

${\displaystyle V.R={\frac {V_{no-load}-V_{full-load}}{V_{no-load}}}}$

### Characteristic Impedance

The characteristic impedance or surge impedance (usually written Z0) of a uniform transmission line is the ratio of the amplitudes of voltage and current of a single wave propagating along the line; that is, a wave travelling in one direction in the absence of reflections in the other direction.

## Line Parameters of AC transmission

The AC transmission has four line parameters, these are the series resistance & inductance, and shunt capacitance and admittance. These parameters are responsible for distinct behavior of voltage and current waveforms along the transmission line. Line parameters are generally represented in their respective units per Km of length in transmission lines. So these parameters actually depend upon the geometric alignment of transmission lines (no of conductor used, shape of conductors, physical spacing between conductors and height above the ground etc).These parameters are independent of current and voltage of any of the sending or receiving ends.

### Series resistance

The electrical resistance of an object is a measure of its opposition to the flow of electric current. The inverse quantity is electrical conductance, and is the ease with which an electric current passes. Electrical resistance shares some conceptual parallels with the notion of mechanical friction. The SI unit of electrical resistance is the ohm (Ω), while electrical conductance is measured in siemens (S).

The resistance of an object depends in large part on the material it is made of—objects made of electrical insulators like rubber tend to have very high resistance and low conductivity, while objects made of electrical conductors like metals tend to have very low resistance and high conductivity. This material dependence is quantified by resistivity or conductivity. However, resistance and conductance are extensive rather than bulk properties, meaning that they also depend on the size and shape of an object. For example, a wire's resistance is higher if it is long and thin, and lower if it is short and thick. All objects show some resistance, except for superconductors, which have a resistance of zero.

The resistance (R) of an object is defined as the ratio of voltage across it (V) to current through it (I), while the conductance (G) is the inverse:

${\displaystyle R={V \over I},\qquad G={I \over V}={\frac {1}{R}}}$

For a wide variety of materials and conditions, V and I are directly proportional to each other, and therefore R and G are constants (although they will depend on the size and shape of the object, the material it is made of, and other factors like temperature or strain). This proportionality is called Ohm's law, and materials that satisfy it are called ohmic materials. In other cases, such as a transformer, diode or battery, V and I are not directly proportional. The ratio V/I is sometimes still useful, and is referred to as a "chordal resistance" or "static resistance",[6][7] since it corresponds to the inverse slope of a chord between the origin and an I–V curve. In other situations, the derivative ${\displaystyle {\frac {dV}{dI}}\,\!}$  may be most useful; this is called the "differential resistance".

Transmission lines, as they consist of conducting wires, have electrical resistance that can't be neglected at all.

### Series Inductance

Line inductance

When current flows within a conductor, magnetic flux is set up. With the variation of current in the conductor, the number of lines of flux also changes, and an emf is induced in it (Faraday’s Law). This induced emf is represented by the parameter known as inductance. It is customary to use the symbol L for inductance, in honour of the physicist Heinrich Lenz.

In the SI system, the unit of inductance is the henry (H), which is the amount of inductance which causes a voltage of 1 volt when the current is changing at a rate of one ampere per second. It is named for Joseph Henry, who discovered inductance independently of Faraday.[8]

The flux linking with the conductor consists of two parts, namely, the internal flux and the external flux :

• The internal flux is induced due to the current flow in the conductor.
• The external flux produced around the conductor is due to its own current and the current of the other conductors place around it. The total inductance of the conductor is determined by the calculation of the internal and external flux.

The transmission line wiring is also inductive in nature and, the inductance of a single circuit line can be given mathematically by : ${\displaystyle L={\frac {\mu _{0}}{2\pi }}ln{\frac {D}{r\prime }}H/m}$

Where,

• D is the physical spacing between the conductors.
• ${\displaystyle r\prime =re^{-1/4}}$  is the radius of the fictitious conductor having no internal flux linkages but with the same inductace as the original conductor of radius r. A quantity of ${\displaystyle e^{-1/4}}$ (=0.7788 appx.) is multiplied with the actual radius of conductor in order to account for the internal flux linkages(applicable to solid round conductors only)[9]
• ${\displaystyle \mu _{0}}$  is the permeability of free space and ${\displaystyle {\mu _{0}}=4\pi \times 10^{-7}H/m}$ .

For transposed lines with two or more phases, the inductance between any two lines can be calculated using : ${\displaystyle L={\frac {\mu _{0}}{2\pi }}ln{\frac {D_{GMD}}{r\prime }}H/m}$ .

Where, ${\displaystyle D_{GMD}}$  is the geometric mean distance 0f the conductors.

If the lines are not properly transposed, the inductances become unequal and contain imaginary terms due to mutual inductances. In case of proper transposition, all the conductors occupy the available positions equal distance and thus the imaginary terms are canceled out.And all the line inductances become equal.

### Shunt Capacitance

Line capacitance

Capacitance is the ratio of the change in an electric charge in a system to the corresponding change in its electric potential.The capacitance is a function only of the geometry of the design (e.g. area of the plates and the distance between them) and the permittivity of the dielectric material between the plates of the capacitor. For many dielectric materials, the permittivity and thus the capacitance, is independent of the potential difference between the conductors and the total charge on them.

The SI unit of capacitance is the farad (symbol: F), named after the English physicist Michael Faraday. A 1 farad capacitor, when charged with 1 coulomb of electrical charge, has a potential difference of 1 volt between its plates.[10] The reciprocal of capacitance is called elastance.

There are two closely related notions of capacitance self capacitance and mutual capacitance :

• For an isolated conductor, there exists a property called self capacitance, which is the amount of electric charge that must be added to an isolated conductor to raise its electric potential by one unit (i.e. one volt, in most measurement systems).[11] The reference point for this potential is a theoretical hollow conducting sphere, of infinite radius, with the conductor centered inside this sphere. Any object that can be electrically charged exhibits self capacitance. A material with a large self capacitance holds more electric charge at a given voltage than one with low self capacitance.
• The notion of mutual capacitance is particularly important for understanding the operations of the capacitor, one of the three elementary linear electronic components (along with resistors and inductors).In electrical circuits, the term capacitance is usually a shorthand for the mutual capacitance between two adjacent conductors, such as the two plates of a capacitor.

Transmission line conductors constitute a capacitor between them, exhibiting mutual capacitance. The conductors of the transmission line act as a parallel plate of the capacitor and the air is just like a dielectric medium between them. The capacitance of a line gives rise to the leading current between the conductors. It depends on the length of the conductor. The capacitance of the line is proportional to the length of the transmission line. Their effect is negligible on the performance of lines with short length and low voltage. In the case of high voltage and long lines, it is considered as one of the most important parameters. The shunt capacitance of the line is responsible for Ferranti effect.[12]

The capacitance of a single phase transmission line can be given mathematically by : ${\displaystyle C_{ab}={\frac {\pi \epsilon _{0}}{ln{\frac {D}{r}}}}F/m}$

Where,

• D is the physical spacing between the conductors.
• r is the radius of each conductor.
• ${\displaystyle \epsilon _{0}}$  is the permittivity of air and ${\displaystyle {\epsilon _{0}}=8.854\times 10^{-12}}$

For lines with two or more phases, the capacitance between any two lines can be calculated using : ${\displaystyle C={\frac {\pi \epsilon _{0}}{ln{\frac {D_{GMD}}{r}}}}F/m}$

Where, ${\displaystyle D_{GMD}}$  is the geometric mean distance 0f the conductors.

The effect of self capacitance, on transmission line are generally neglected because the conductors are not isolated and thus there exists no detectable self capacitance.

In electrical engineering, admittance is a measure of how easily a circuit or device will allow a current to flow. It is defined as the reciprocal of impedance. The SI unit of admittance is the siemens (symbol S); the older, synonymous unit is mho, and its symbol is ℧ (an upside-down uppercase omega Ω). Oliver Heaviside coined the term admittance in December 1887.[13]

${\displaystyle Y\equiv {\frac {1}{Z}}\,}$

where

Y is the admittance, measured in siemens
Z is the impedance, measured in ohms

Resistance is a measure of the opposition of a circuit to the flow of a steady current, while impedance takes into account not only the resistance but also dynamic effects (known as reactance). Likewise, admittance is not only a measure of the ease with which a steady current can flow, but also the dynamic effects of the material's susceptance to polarization:

${\displaystyle Y=G+jB\,}$

where

• ${\displaystyle Y}$  is the admittance, measured in siemens.
• ${\displaystyle G}$  is the conductance, measured in siemens.
• ${\displaystyle B}$  is the susceptance, measured in siemens.
• ${\displaystyle j^{2}=-1}$

The dynamic effects of the material's susceptance relate to the universal dielectric response, the power law scaling of a system's admittance with frequency under alternating current conditions.

In the context of electrical modeling of transmission lines, shunt components that provide paths of least resistance in certain models are generally specified in terms of their admittance.Transmission lines can span hundreds of kilometers, over which the line's capacitance can affect voltage levels. For short length transmission line analysis, this capacitance can be ignored and shunt components are not necessary in the model. Lines with more length , contain a shunt admittance governed by[14]

${\displaystyle Y=yl=j\omega Cl}$

where

y – shunt admittance per unit length

l – length of line

C – capacitance of line

## Modelling of Transmission Lines

### Two Port Networks

Figure 1: Example two-port network with symbol definitions. Notice the port condition is satisfied: the same current flows into each port as leaves that port.

A two-port network (a kind of four-terminal network or quadripole) is an electrical network (circuit) or device with two pairs of terminals to connect to external circuits. Two terminals constitute a port if the currents applied to them satisfy the essential requirement known as the port condition: the electric current entering one terminal must equal the current emerging from the other terminal on the same port.[15][16] The ports constitute interfaces where the network connects to other networks, the points where signals are applied or outputs are taken. In a two-port network, often port 1 is considered the input port and port 2 is considered the output port.

The two-port network model is used in mathematical circuit analysis techniques to isolate portions of larger circuits. A two-port network is regarded as a "black box" with its properties specified by a matrix of numbers. This allows the response of the network to signals applied to the ports to be calculated easily, without solving for all the internal voltages and currents in the network. It also allows similar circuits or devices to be compared easily. For example, transistors are often regarded as two-ports, characterized by their h-parameters (see below) which are listed by the manufacturer. Any linear circuit with four terminals can be regarded as a two-port network provided that it does not contain an independent source and satisfies the port conditions.

### Transmission Matrix & ABCD Parameters

"Black box" model for transmission line

Oftentimes, we are only interested in the terminal characteristics of the transmission line, which are the voltage and current at the sending and receiving ends, for performance analysis of the line. The transmission line itself is then modeled as a "black box" and a 2 by 2 transmission matrix is used to model its behavior, as follows[17][18]

${\displaystyle {\begin{bmatrix}V_{\mathrm {S} }\\I_{\mathrm {S} }\\\end{bmatrix}}={\begin{bmatrix}A&B\\C&D\\\end{bmatrix}}{\begin{bmatrix}V_{\mathrm {R} }\\I_{\mathrm {R} }\\\end{bmatrix}}}$

Derivation

This equation in matrix form, consists of two individual equations as stated below :

${\displaystyle V_{S}=AV_{R}+BI_{R}}$

${\displaystyle I_{S}=CV_{R}+DI_{R}}$

Where,

${\displaystyle V_{S}}$  is the sending end voltage

${\displaystyle V_{R}}$  is the receiving end voltage

${\displaystyle I_{S}}$  is the sending end current

${\displaystyle I_{R}}$  is the receiving end current

ABCD Parameters
Parameters Parameter Name Value Unit
A Voltage ratio ${\displaystyle \left.{\frac {V_{S}}{V_{R}}}\right|_{I_{R}=0}}$  Unit less
B Circuit resistance ${\displaystyle \left.{\frac {V_{S}}{I_{R}}}\right|_{V_{R}=0}}$  Ohm (Ώ)
C Circuit conductance ${\displaystyle \left.{\frac {I_{S}}{V_{R}}}\right|_{I_{R}=0}}$  Mho (${\displaystyle \mho }$ )
D Current ratio ${\displaystyle \left.{\frac {I_{S}}{I_{R}}}\right|_{V_{R}=0}}$  Unit less

properties

The line is assumed to be a reciprocal, symmetrical network, meaning that the receiving and sending labels can be switched with no consequence. The transmission matrix T also has the following properties:

• ${\displaystyle \det(T)=AD-BC=1}$
• ${\displaystyle A=D}$

The parameters A, B, C, and D differ depending on how the desired model handles the line's resistance (R), inductance (L), capacitance (C), and shunt (parallel, leak) conductance G. The four main models are the short line approximation, the medium line approximation, the long line approximation (with distributed parameters), and the lossless line. In all models described, a capital letter such as R refers to the total quantity summed over the line and a lowercase letter such as c refers to the per-unit-length quantity.

## Classification of AC transmission line

### Classification Overview

The AC transmission line has resistance R, inductance L, capacitance C and the shunt or leakage conductance G. These parameters along with the load and the transmission line determine the performance of the line. The termperformance means the sending end voltage, sending end currents, sending end factor, power loss in the line, efficiency of the transmission line, regulate and limit of power flow during efficiency and transmission, regulation and limits of power during steady state and transient condition. AC transmission line is generally categorized into three classes[19]

• Short Transmission Line (line length ≤ 60 Km)
• Medium Transmission Line (80 Km ≤ Line length ≤ 250 Km)
• Long Transmission Line (Line length ≥ 250 Km)

The classification of the transmission line depends on the frequency of power transfer and is an assumption made for ease of calculation of line performace parameters & it's losses[20]. And because this, the range of length for the categorization of transmission line is not rigid. The ranges of length may vary (a little), and all of them are valid in their own areas of approximation.

### Basis of classification

Comparision of Wavelength to the Line length

Current and voltage propagate in a transmission line with a speed equal to the speed of light (c) i.e. appx. ${\displaystyle 3\times 10^{8}m/sec=3\times 10^{5}km/sec}$  and the frequency (f) of voltage or current is 50Hz ( although in the Americas and parts of Asia it is typically 60 Hz)[21][22]

Therefore wavelength (λ) can be calculated as below :

${\displaystyle f\lambda =c}$

or, ${\displaystyle \lambda ={\frac {c}{f}}}$

or, ${\displaystyle \lambda ={\frac {3\times 10^{5}}{50}}=6000Km}$

Now, A transmission line with 60 km of length is very very small( ${\displaystyle {\tfrac {1}{100}}}$  times) when compared with Wavelength i.e. 6000 km. Up to 240 km (${\displaystyle {\tfrac {1}{25}}}$  times of wavelength) (250 Km is taken for easy remembering) length of line, current or voltage waveform is so small that it can be approximated to straight line for all practical purposes.For line length of about 240 km parameters are assumed to be lumped (though practically these parameters are always distributed) . Therefore the response of transmission line for a length up to 250 km can be considered linear and hence the equivalent circuit of line can be approximated to linear circuit. But if the length of line is more than 250 km say 400 Km i.e. ${\displaystyle {\tfrac {1}{15}}}$  times of wavelength , then the waveform of current or voltage can not be considered liner and therefore we need to use integration for the analysis of these lines.

1. For the lines of upto 60 Km of length are so short, that the effect of shunt parameters are nearly undetectable throughout the line. And hence, these linear lines are categorized as Short Transmission Lines.
2. For the lines of effective length in between 60 Km to 250 Km, the effect of shunt parameters can not be neglected. And hence, they are assumed as lumped either at the middle of the line (a nominal T representation) or at the two ends of the line (a nominal Π representation). These linear lines are categorized as Medium Transmission Lines
3. For transmission lines of effective length above 250 Km, the equivalent circuit can not be considered as liner. The parameters are distributed and rigorous calculations are required for performance analysis. These non-linear lines are categorized as Long Transmission Lines.

## Short Transmission Line

Approximated model for Short Transmission Line

Phasor Diagram of Short Transmission Line

The transmission lines which have length less than 60 km are generally referred as short transmission lines. For its short length, parameters like electrical resistance, impedance and inductance of these short lines are assumed to be lumped.The shunt capacitance for a short line is almost negligible and thus, are not taken into account (or assumed to be zero).

So, by considering the equivalent circuit model for short transmission line, the transmission matrix can be obtained as follows:

${\displaystyle {\begin{bmatrix}V_{\mathrm {S} }\\I_{\mathrm {S} }\\\end{bmatrix}}={\begin{bmatrix}1&Z\\0&1\\\end{bmatrix}}{\begin{bmatrix}V_{\mathrm {R} }\\I_{\mathrm {R} }\\\end{bmatrix}}}$

(3)

Therefore the ABCD parameters are given by :

A = D =1, B = Z Ω and C = 0

## Medium Transmission Line

The transmission line having its effective length more than 80 km but less than 250 km is generally referred to as a medium transmission line. Due to the line length being considerably high, shunt capacitance along with admittance Y of the network does play a role in calculating the effective circuit parameters, unlike in the case of short transmission lines. For this reason the modeling of a medium length transmission line is done using lumped shunt admittance along with the lumped impedance in series to the circuit.

Counterintuitive behaviors of medium-length transmission lines:

• voltage rise at no load or small current (Ferranti effect)
• receiving-end current can exceed sending-end current

These lumped parameters of a medium length transmission line can be represented using two different models, namely :

### Nominal Π representation

Medium Transmission Line (Π representation)

Phasor diagram of Medium Transmission Line (Nominal Π Representation)

In case of a nominal Π representation, the total lumped shunt admittance is divided into 2 equal halves, and each half with value Y ⁄ 2 is placed at both the sending & receiving end, while the entire circuit impedance is lumped in between the two halves. The circuit, so formed resembles the symbol of pi (Π) , hence is known as the nominal Π (or Π network representation) of a medium transmission line. It is mainly used for determining the general circuit parameters and performing load flow analysis.

Derivation of ABCD parameters for this Representation

Applying KCL at the two shunt ends, we get

${\displaystyle I_{S}=I_{1}+I_{2}={\frac {Y}{2}}V_{S}+{\frac {Y}{2}}V_{R}+I_{R}}$

${\displaystyle I_{1}\&I_{3}}$  are the currents through the shunt capacitances at the sending and receiving end respectively whereas ${\displaystyle I_{2}}$  is the current through the series impedance.

Again,

${\displaystyle V_{S}=ZI_{2}+V_{R}=Z(V_{R}{\frac {Y}{2}}+I_{R})+I_{R}}$

or,

${\displaystyle V_{S}=(1+{\frac {YZ}{2}})V_{R}+ZI_{R}}$

(4)

So, by substituting we get :

${\displaystyle I_{S}={\frac {Y}{2}}[(1+{\frac {YZ}{2}})V_{R}+ZI_{R}]+{\frac {Y}{2}}V_{R}+I_{R}}$

or,

${\displaystyle I_{S}=Y(1+{\frac {YZ}{4}})V_{R}+(1+{\frac {YZ}{2}})I_{R}}$

(5)

The equation obtained thus, eq(4) & (5) can be written into matrix form as follows :

${\displaystyle {\begin{bmatrix}V_{S}\\I_{S}\\\end{bmatrix}}={\begin{bmatrix}1+{\frac {YZ}{2}}&Z\\Y(1+{\frac {YZ}{4}})&1+{\frac {YZ}{2}}\end{bmatrix}}{\begin{bmatrix}V_{R}\\I_{R}\\\end{bmatrix}}}$

(6)

so, the ABCD parameters are :

A = D =${\displaystyle (1+{\frac {YZ}{2}})}$  per unit

B =Z Ω

C = ${\displaystyle Y(1+{\frac {YZ}{4}})\mho }$

### Nominal T representation

Medium Transmission Line (T representation)

Phasor diagram of Medium Transmission Line (Nominal T Representation)

## Long Transmission Line

Generalized model of Long Transmission Line

A transmission line having a length more than 250 km is considered as a long transmission line. Unlike short and medium lines the line parameters of long transmission line are assumed to be distributed at each point of line uniformly. Thus modeling of long line is somewhat difficult. But few approaches can be made on the basis of length and values of line parameters. For a long transmission line, it is considered that the line may be divided into various sections, and each section consists of an inductance, capacitance, resistance and conductance, as shown in the RLC (resistance and inductance in series, with shunt capacitace) cascade model .

Long Transmission Line (Series RLC Cascade Model)

Considering a bit smaller part of a long transmission line having length dx situated at a distance x from the receiving end. Series impedance of the line is represented by zdx and ydx is the shunt impedance of the line. Due to charging current and corona loss the current is not uniform along the line. Voltage is also different in different parts of the line because of inductive reactance.

Where,

z – series impedance per unit length, per phase

y – shunt admittance per unit length, per phase to neutral

${\displaystyle \Delta V=I_{z}\Delta x\Rightarrow {\frac {\Delta V}{\Delta x}}=I_{z}}$

Again, as ${\displaystyle \Delta x\rightarrow 0}$

${\displaystyle {\frac {\Delta V}{\Delta x}}=I_{z}}$

Combining these two we have,

${\displaystyle I={\frac {1}{z}}{\frac {dV}{dx}}={{\frac {A_{1}}{\sqrt {\frac {z}{y}}}}{e^{x{\sqrt {yz}}}}}+{{\frac {A_{2}}{\sqrt {\frac {z}{y}}}}{e^{-x{\sqrt {yz}}}}}}$

(16)

The following two quantities are defined as,

${\displaystyle Z_{c}={\sqrt {\frac {z}{y}}}\Omega }$  , which is called the characteristic impedance

${\displaystyle \gamma ={\sqrt {yz}}}$  , which is called the propagation constant

${\displaystyle V=A_{1}e^{\gamma x}\quad +\quad A_{2}e^{-\gamma x}}$

(17)

${\displaystyle I={\frac {A_{1}}{Z_{c}}}e^{\gamma x}\quad +\quad {\frac {A_{2}}{Z_{c}}}e^{-\gamma x}}$

(18)

Now, at ${\displaystyle x=0}$  we have, ${\displaystyle V=V_{r}}$  and ${\displaystyle I=I_{r}}$

Therefore by putting ${\displaystyle x=0}$  at eq.(17) & eq.(18) we get,

${\displaystyle V_{r}=A_{1}\quad +\quad A_{2}}$

(19)

${\displaystyle I_{r}={\frac {A_{1}}{Z_{c}}}\quad +\quad {\frac {A_{2}}{Z_{c}}}}$

(20)

Solving eq.(19) & eq.(20) we get the following values for ${\displaystyle A_{1}\&A_{2}}$  :

${\displaystyle A_{1}={\frac {V_{r}+Z_{c}I_{r}}{2}}\&A_{2}={\frac {V_{r}+Z_{c}I_{r}}{2}}}$

(21)

Also, for ${\displaystyle l=x}$ , we have ${\displaystyle V=V_{S}}$  and ${\displaystyle I=I_{S}}$ .

Therefore by replacing x by l we get,

${\displaystyle V_{s}={\frac {V_{r}+Z_{c}I_{r}}{2}}e^{\gamma l}\quad +\quad {\frac {V_{r}-Z_{c}I_{r}}{2}}e^{-\gamma l}}$

(22)

${\displaystyle I_{s}={\frac {{\frac {V_{r}}{Z_{c}}}+I_{r}}{2}}e^{\gamma l}\quad +\quad {\frac {{\frac {V_{r}}{Z_{c}}}-I_{r}}{2}}e^{-\gamma l}}$

(23)

Where,

${\displaystyle {\frac {V_{r}+Z_{c}I_{r}}{2}}e^{\gamma l}}$  is called incident voltage wave

${\displaystyle {\frac {V_{r}-Z_{c}I_{r}}{2}}e^{-\gamma l}}$  is called reflected voltage wave

We can rewrite the eq.(22) & eq.(23) as,

${\displaystyle V_{s}=V_{r}cosh(\gamma l)+Z_{c}I_{r}sinh(\gamma l)}$

(24)

${\displaystyle I_{s}={\frac {V_{r}}{Z_{c}}}sinh(\gamma l)+I_{r}cosh(\gamma l)}$

(25)

So, by cosidering the corresponding analogy for long transmission line, the obtained equations i.e. eq.(24) eq.(25) can be written into matrix form as follows:

${\displaystyle {\begin{bmatrix}V_{\mathrm {S} }\\I_{\mathrm {S} }\\\end{bmatrix}}={\begin{bmatrix}cosh\ \gamma l&Zc\ sinh\ \gamma l\\{\frac {sinh\ \gamma l}{Z_{c}}}&cosh\ \gamma l\end{bmatrix}}{\begin{bmatrix}V_{\mathrm {R} }\\I_{\mathrm {R} }\\\end{bmatrix}}}$

(26)

The ABCD parameters are given by :

A = D =${\displaystyle cosh\ \gamma l}$

B =${\displaystyle Zc\ sinh\ \gamma l}$

C =${\displaystyle {\frac {sinh\ \gamma l}{Z_{c}}}sinh\ \gamma l}$

### Π Representation approach

The ABCD parameters of this long line can be defined like medium transmission line as :

A = D =${\displaystyle (1+{\frac {Y\prime Z\prime }{2}})}$  per unit

B =Z′ Ω

C = ${\displaystyle Y(1+{\frac {Y\prime Z\prime }{4}})\mho }$

Comparing it with the ABCD parameters of cascaded long transmission model, we can write :

• ${\displaystyle Z\prime =Z_{C}sinh\gamma l={\sqrt[{}]{\frac {z}{y}}}sinh\gamma l=zl{\frac {sinh\gamma l}{l{\sqrt[{}]{yz}}}}=Z{\frac {sinh\gamma l}{\gamma l}}\Omega }$

Where Z = zl, is thetotal impedence of the line.

• ${\displaystyle cosh\gamma l=1+{\frac {Y\prime Z\prime }{2}}={\frac {Y\prime }{2}}Z_{C}sinh\gamma l+1}$

### Travelling waves in Transmission Line

RLC ladder model of a Long Transmission Line to understand Travelling Waves

Travelling waves are the current and voltage waves which travel from the sending end of a transmission line to the other end.

When the switch is closed at the transmission line's starting end, voltage will not appear instantaneously at the other end. This is caused by the transient behavior of inductor and capacitors that are present in the transmission line. The transmission lines may not have physical inductor and capacitor elements but the effects of inductance and capacitance exists in a line. Therefore, when the switch is closed the voltage will build up gradually over the line conductors. This phenomenon is usually called as the voltage wave is travelling from transmission line's sending end to the other end. And similarly the gradual charging of the capacitances happens due to the associated current wave.

If the switch is closed at any instant of time, the voltage at load does not appear instantly. The 1st section will charge first and then it will charge the next section. Until and unless a section gets charged the successive section will not be charged .thus this process is a gradual one. It can be realized such that several water tanks are placed connectively and water flows from 1st tank to last tank.

## References

1. ^ "A Primer on Electric Utilities, Deregulation, and Restructuring of U.S. Electricity Markets" (pdf). United States Department of Energy Federal Energy Management Program (FEMP). May 2002. Retrieved October 30, 2018.
2. ^ Stephen W. Fardo & Dale R. Patrick, Electrical Power Systems Technology, Third Edition, Taylor & Francis Ltd. ,USA, 2008, ISBN 978-1-4398-0027-0, Chapter 8 Power Distribution Fundamentals
3. ^ J. F. Wilson, Ferranti and the British Electrical Industry, 1864–1930, Manchester University Press, 1988 ISBN 0-7190-2369-6 page 44
4. ^
5. ^
6. ^ Forbes T. Brown (2006). Engineering System Dynamics. CRC Press. p. 43. ISBN 978-0-8493-9648-9.
7. ^ Kenneth L. Kaiser (2004). Electromagnetic Compatibility Handbook. CRC Press. pp. 13–52. ISBN 978-0-8493-2087-3.
8. ^
9. ^ CL Wadhwa, Electrical Power Systems, Seventh Multicolour Edition, New Age International (P) Limited , New Delhi, 2017, ISBN 978-93-86070-19-7, Chapter 2 Line Constant Calculations
10. ^ "Definition of 'farad'". Collins.
11. ^ William D. Greason (1992). Electrostatic discharge in electronics. Research Studies Press. p. 48. ISBN 978-0-86380-136-5. Retrieved December 4, 2011.
12. ^ CL Wadhwa, Electrical Power Systems, Seventh Multicolour Edition, New Age International (P) Limited , New Delhi, 2017, ISBN 978-93-86070-19-7, Chapter 3 Capacitance of Transmission Lines
13. ^ Ushida, Jun; Tokushima, Masatoshi; Shirane, Masayuki; Gomyo, Akiko; Yamada, Hirohito (2003). "Immittance matching for multidimensional open-system photonic crystals". Physical Review B. 68 (15). arXiv:cond-mat/0306260. Bibcode:2003PhRvB..68o5115U. doi:10.1103/PhysRevB.68.155115.
14. ^ J. Glover, M. Sarma, and T. Overbye, Power System Analysis and Design, Fifth Edition, Cengage Learning, Connecticut, 2012, ISBN 978-1-111-42577-7, Chapter 5 Transmission Lines: Steady-State Operation
15. ^ Gray, §3.2, p. 172
16. ^ Jaeger, §10.5 §13.5 §13.8
17. ^ Electrical Power Systems : Design and Analysis, Md. E.El-Hawary, ISBN 0-7803-1140X, p.157.
18. ^ Ghosh, p.353.
19. ^ NPTEL courses Chapter 2 : Transmission Line Models (https://nptel.ac.in/courses/117104071/chap2.pdf)
20. ^ CL Wadhwa, Electrical Power Systems, Seventh Multicolour Edition, New Age International (P) Limited , New Delhi, 2017, ISBN 978-93-86070-19-7, Chapter 2 Performance of Lines
21. ^ A.C. Monteith , C.F. Wagner (ed), Electrical Transmission and Distribution Reference Book 4th Edition, Westinghouse Electric Corporation 1950, page 6
22. ^ https://en.wikipedia.org/wiki/Utility_frequency